 Open Access
 Authors : Snehal B. Sahare , U. G. Bonde
 Paper ID : IJERTV9IS020068
 Volume & Issue : Volume 09, Issue 02 (February 2020)
 Published (First Online): 11022020
 ISSN (Online) : 22780181
 Publisher Name : IJERT
 License: This work is licensed under a Creative Commons Attribution 4.0 International License
Transient Stability Enhancement in MultiMachine Power System by using Power System Stabilizer (Pss) and Static Var Compensator (Svc)
Snehal B. Sahare
PG Scholar, Department of Electrical Engineering Shri Sai College of Engineering & Technology Bhadrawati, Maharashtra, India.
U. G. Bonde
Professor, Department of Electrical Engineering Shri Sai College of Engineering & Technology
Bhadrawati, Maharashtra, India.
Abstract – In recent years, power demand has increased substantially while the expansion of power generation and transmission has been severely limited due to limited resources and environmental restrictions. As a consequence, some transmission lines are heavily loaded and the system stability becomes a power transferlimiting factor. Flexible AC transmission systems (FACTS) controllers have been mainly used for solving various power system steady state control problems. However, recent studies reveal that FACTS controllers could be employed to enhance power system stability in addition to their main function of power flow control.
This paper presents a fundamental analysis of the application of first generation FACT device i.e., Static VAR compensators (SVCs) and power system stabilizers (PSSs) for stabilizing power systems. Basic SVC control strategies are examined in terms of enhancing the dynamic and transient stabilities. SVC is basically a shunt connected static var generator whose output is adjusted to exchange capacitive or inductive current so as to maintain or control specific power variable; typically, the control variable is the SVC bus voltage.
Firstly, to design a controller for SVC devices on transmission lines, a Four Machine Infinite Bus (FMIB) system is modeled. A MATLAB simulation has been carried out to demonstrate the performance of the four machine transmission bus system.
Keywords – FACTS, MultiMachine System, PSS, SVC, Transient Stability.

INTRODUCTION
Modern power systems are increasingly complex nonlinear interconnected networks comprising interconnected generator power plants, transformers and transmission lines with differences in loads. The interconnection of smaller subsystems is useful in reducing operating costs (e.g. fuel costs, sharing resources) and variety of loads improves the reliability of the system [1]. However, these possess technical challenges like low frequency electromechanical oscillation caused by electrical disturbances [2]. The power system stability is that the ability of the system to come back to its original operating condition after the disturbance [3]. In modern power systems, increased in the power demand results the overloading in long transmission lines (above normal limits), exacerbating the problem of transient stability, which has become a serious limiting factor in electrical engineering.
The transient stability of a system is defined as the ability of the system to maintain the system in stable condition after occurrence of the large disturbances, like fault and switching
of lines. There are many ways for improving transient stability, including circuit breakers, fastacting exciters and reduction within the transfer reactance of the system [1]. Under small disturbances, to remain synchronization the machine requires positive damping, generally from a power system stabilizer (PSS) provides positive damping to the system, which is one of the most common controls used to damp out oscillations.
The main role of PSS is to introduce modeling signal acting through the excitation system for oscillation damping [4]. It should be capable of providing stabilization signals over a broad range of operating conditions and disturbances; however, within nonlinear systems, the function of PSS is limited [5]. Many complex power systems are now stabilized using Flexible Alternating Current Transmission System (FACTS), which can control network conditions with optimum speed and enhance transient, voltage and steady state stabilities [6].
There are numerous classes of FACTS controllers, including shunt, series, combined seriesseries and combined seriesshunt types. FACTS devices include a group of multiple controllers used to regulate system parameters like damping oscillation at different frequency, phase angle, voltage, current and impedance [7]. In this paper, SVC is discussed. It is a shunt type, used to connect as a controller which enhances the transient stability and damping the power oscillation with more reliable operation [8], [9].
The organization of this paper is as follows: Section II power system stabilizer PSS structure and the effect of damping oscillation; Section III models of static Var compensator SVC and explains SVC principles and its effectiveness to improve damping oscillation and explain the structure of the SVC controller; and Section IV presents the conclusion of the work.

POWER SYSTEM STABILIZER (PSS)
These are controllers with the ability to control synchronous machine stability through the excitation system by employing highspeed exciters and continuously acting voltage regulators. The PSS (Fig.1) adds damping to the generator units characteristic electromechanical oscillations by modulating the generator excitation to develop components of electrical torque in phase with rotor speed deviations. The PSS thus contributes to the enhancement of smallsignal stability of power systems. Fixed structure stabilizers generally provide acceptable dynamic performance.
Fig.1. Block diagram of the PSS.

SpeedBased () Stabilizer
These are stabilizers that employ a direct measurement of shaft speed. Runout compensation must be inherent to the method of measuring the speed signal to minimize noise caused by shaft runout (lateral movement) and other sources.
While stabilizers supported direct measurement of shaft speed is used on several thermal units, this kind of stabilizer has many limitations. The primary disadvantage is the need to use a torsional filter to attenuate the torsional components of the stabilizing signal. This filter introduces a phase lag at lower frequencies which has a destabilizing effect on the "exciter mode", thus imposing a maximum limit on the allowable stabilizer gain. In several cases, this is often restrictive and limits the overall effectiveness of the stabilizer in damping system oscillations. In addition, the stabilizer has to be customdesigned for each type of generating Power Based (P) PSS unit depending on its torsional characteristics.

PowerBased (P) Stabilizer
Due to the simple structure of power measurement and its relationship to shaft speed, it had been thoughtabout to be a natural candidate as an input signal to early stabilizers. The equation of motion for the rotor is written as follows:
= 1 ( )

IntegralofAccelerating Power (P) Stabilizer
The limitations inherent in the other stabilizer structures led to the development of stabilizers that measure the accelerating power of the generator. Due to the complexity of the design, and the need for customization at each location, a method of indirectly deriving the accelerating power was developed as shown in fig.2.
Fig.2. Accelerating Power PSS Model.
The principle of this stabilizer is illustrated by rewriting equation (1) in terms of the integral of power.
= 1 ( )
2
(2)
The integral of mechanical power is related to electrical power and shaft speed as given bellow:
= 2 +
(3)
(1)
2The P stabilizer makes use of the (3) simulate a signal proportional to the integral of change in mechanical power by
Where, H = inertia constant; Pm = change in mechanical
power input; Pe = change in electric power output and = speed deviation
If variations of mechanical power are neglected, this equation implies that, signals are proportional to shaft acceleration (i.e. one that leads speed changes by 90Â°) is available from the scaled measurement of electrical power. This principle was implemented as the basic for many several stabilizer designs. In combination with both high and lowpass filtering, the stabilizing signal derived in this manner might
adding signals proportional to shaftspeed change and integral of electrical power change. On horizontal shaft units, this signal will contain torsional oscillations unless a filter is used. Because mechanical power changes are relatively slow, the derived integral of mechanical power signal can be conditioned with a lowpass filter to attenuate torsional frequencies. The overall transfer function for deriving the integralof accelerating power signal from measurement of electrical power and shaft speed is given bellow
( )
= + () [ + ()]
provide pure damping torque at specifically one electromechanical frequency.
(4)
2
2
2
But at a same time this design has two major disadvantages. First, it cant be set to produce a pure damping contribution at more than one frequency and thus for units affected by both local and interarea modes a compromise is needed. The second limitation is that an unwanted stabilizer output is made whenever mechanical power changes occur. This severely limits the gain and output limits that will be used with these units. Even modest loading and unloading rates produce large terminal voltage and reactive power variations, unless stabilizer gain is severely restricted. Many powerbased stabilizers are still in operation though theyre rapidly replaced by units supported the integralof accelerating power design.
Where, G(s) is the lowpass filters transfer function.
The major advantage of a P stabilizer is that there is no requirement for a torsional filter in the main stabilizing path including the Pe signal. This alleviates the exciter mode stability problem, thereby permitting a higher stabilizer gain that result in better damping of system oscillations. A conventional endofshaft speed measurement or compensated frequency signal can be used with this structure.


STATIC VAR COMPENSATORS (SVCS)
The singleline diagram of a SVC and a simplified block diagram of its control system is shown in fig 3. Static Var compensators (SVCs) rated at 50 ~ 300 MVar, consisting of voltage source inverters using gateturnoff (GTO) thyristors, are employed in improving power factor and stabilizing
transmission systems. By controlling the amount of reactive power injected into or absorbed from the power system the SVC regulates voltage at its terminals. The SVC generates reactive power (SVC capacitive) when system voltage is low
Where, VS is the rms voltage of the supply and O is its angular frequency. The above assumptions lead to the following ac voltage of the SVC:
and absorbs the reactive power (SVC inductive) when the
[ ] =cos(0 + )
3
3
2 [cos( 2/3 + )] (6)
system voltage is high. The SVC can adjust the amplitude of the ac voltage of the inverters by pulsewidth modulation
0
cos(0 + 2/3 + )
(PWM) or by controlling the dc bus voltage, thus producing either leading or lagging reactive power.
Where, is the angle of the fundamental ac voltage with respect to the supply voltage, and K is the ac to dc voltage ratio of the SVC.
Fig.4. Model of the SVC: SinglePhase Equivalent.
Using Fig. 2.10, one obtains the following equation:
[ ] = + [] + [ ] (7)
Invoking Assumption 3 results in the following equation for active power:
=
+
+
=
(8)
2
Fig.3. singleline diagram of a SVC and a simplified block diagram of its control system.
A pulsewidthmodulated SVC, in which the dc voltage is
The pq theory can be used to transform,
0 cos
0 cos
+
[ ] [ ] = [ ] (9)controlled to remain at a constant value, responds rapidly to a
+
sin
change in reactive power at the expense of increasing the switching and snubbing losses. High efficiency and high
0
=
(10)
reliability are a priority in practical power system applications
(cos + sin )
of the SVCs. On the other hand, a dc voltagecontrolled SVC, which directly controls the dc capacitor voltage by causing a small amount of active power to flow into or out of the voltagesource inverters, results in less switching and snubbing losses because the switching frequency is low. However, the dc voltagecontrolled SVC is inferior to the Pulse Width Modulated (PWM) SVC in the transient response of reactive power. A model of the SVC based on the pq theory
[17] is developed, and has the ability to deal with the power flow between the ac and dc sides in a transient state.
Modelling of the SVC
The following assumptions are made in modelling the SVC: first, any harmonic voltage caused by the switching operation of the inverters is excluded from the synthesized ac voltage of the SVC; second, the instantaneous amplitude of the fundamental component of the ac voltage is proportional to the instantaneous voltage of the dc capacitor; third, no power loss occurs in the inverters, therefore the active power on the ac side is equal to the active power on the dc side. The assumptions mean that the harmonic voltage caused by fluctuation of the dc voltage is included in the synthesized ac voltage. Assume an ideal threephase power supply given by:
In (9) and (10), ip is an instantaneous active current and iq is an instantaneous reactive current. The instantaneous reactive power which is drawn from the supply, qs is given as:
= . . = . (10)

SVC Control
The SVC can be operated in two different modes: In voltage regulation mode (the voltage is regulated within limits) and in var control mode (the SVC susceptance is kept constant). The block diagram of the control circuit is shown in fig.5. Due to the use Reactive power feedback using a PI controller; it is possible to improve the transient response of the reactive power. The pq transform circuit calculates the instantaneous reactive power qs from the threephase supply voltages and the threephase currents. The calculated reactive power qs and the reference reactive power q*s are applied to the proportionalintegral (PI) controller. The output of the PI controller is a reference signal representing the phase angle *.
The counter produces the phase information, 0t, from a signal generated by the phase locked loop (PLL) circuit. The phase comparator compares with 0t, and determines the
[ ] =cos 0
2 [cos( 2/3)] (5)
time at which the corresponding switching device is turned on or off. The gate control circuit prevents each switching device
3
0
cos(0 + 2/3)
from being switchedon more than once in one cycle due to fast changes in .
Fig.5. Block Diagram of SVC Control Circuit.


SIMULATION RESULTS
The comparison between PSS and SVC was conducted in a multimachine system, as shown in Fig. 6. This system consists of 4 machines and 6 buss. The system was originally
available in MATLAB with two machines and three buses, but in order to consider more cases in this work, the number of machines and buses were increased. Two types of stabilizers can be selected, a generic model using the acceleration power (Pa= difference between mechanical power Pm and output electrical power Peo) and a Multiband stabilizer using the speed deviation (dw). The stabilizer type can be selected by specifying a value (0=No PSS 1=Pa PSS or 2= dw MB PSS) in the PSS constant block. The disturbance applied is three phase fault to ground near a generator 1 on bus 1 at t= 5s; SVC is used as a controller is phaser type, connected to B1 and taking those cases:

Case 1
Fig.6. Test system (4 machine, 6 bus) modeled in Simulink/MATLAB.
both rotor angle with SVC reduced with value is 79 and 67
When comparing between using without PSS and PSS only for a critical clearing time (tc =148 ms), the results show that the system loses stability when utilizing PSS alone, while it remains stable using both SVC and PSS. Fig 710 show the rotor angle difference of G1G2 of the test system, rotor angle difference of G3G4, the terminal voltage on B1 and transmission line active power of G1.

Case 2
Using PSS solely and PSS with SVC (to enhance transient stability and dampen the oscillation), the system remained stable, at clearing time (tc = 147 ms). Table I lists the performance comparison between using (PSS) and (PSS with SVC). Furthermore, Fig 11 and 12 shows the rotor angle difference of G1 and rotor angle difference of G3; SVC settled faster with settling time is (11s and 10.3s) than with only PSS (13s and 13.3s), and the peak amplitude of
degrees, respectively. With only PSS, the corresponding values are 87 and 70 degrees. Fig 13 and 14 show that the terminal voltage on B1 and B6 with SVC oscillated less and stabilized with peak amplitudes of 1.15 p.u and 1.126 p.u, and settling times of 9s and 9s, compared to only PSS with peak amplitudes of 1.29 p.u and 1.222 p.u and settling times of 12s and 12s. Fig 15 and 16 shows the transmission line active power values of G1 and G3; it can be seen that the line with SVC has less oscillation and greater stabilization than that with only PSS.

Case 3
In this case the comparison between using PSS alone and two SVC with PSS in two different locations was made. The first SVC was connected to the system in a location the same as the previous one, and the second was connected near G3 with bus 6. Additionally, Fig 17 and 18 show that
rotor angle difference of G1 and rotor angle difference of G3 with SVC settled faster with settling time is (9s and 9s) than with only PSS (13s and 12.3s), and the peak amplitude of both rotor angle with SVC reduced with values of 78 and 63 degrees. With only PSS the settling time is 13 and 13.3s and the peak amplitude is 86 and 70 degrees. Fig 19 and 20 shows that the terminal voltage on B1and terminal voltage on B6 with SVC oscillates less and stabilizes with peak amplitude (1.145p.u and 1.118p.u) and settling time (8s and 8s) compared to only PSS, where the peak amplitude is (1.29p.u and 1.222p.u) and settling time (12s and 12s). Fig 21 and 22 shows the transmission line active power of G1 and G3.
Fig. 7. Rotor angle difference of G1 to G2.
Fig. 8. Rotor angle difference of G3 to G4.
Fig. 9. Terminal voltage on B1.
Fig. 10. Transmission line active power of G1.
Fig. 11. Rotor angle difference of G1 to G2.
Fig. 12. Rotor angle difference of G3 to G4.
Fig. 13. Terminal voltage on B1.
Fig. 14. Terminal voltage on B6.
Fig. 15. Transmission line active power of G1.
Fig. 16. Transmission line active power of G3.
Fig. 17. Rotor angle difference of G1 to G2.
Fig. 18. Rotor angle difference of G3 to G4.
Fig. 19. Terminal voltage on B1.
Fig. 20. Terminal voltage on B6.
Fig. 21. Transmission line active power of G1.
Fig. 22. Transmission line active power of G3.


CONCLUSION
The SVC enhances system stability by controlling the amount of reactive power injected into or absorbed from the power system. On the other hand, the PSS has for a long time found application in the exciters of synchronous machines as an effective means of damping the generator units characteristic electromechanical oscillations by modulating the generator excitation. Thus, PSSs and FACTS are fast becoming a necessity in power system stability enhancement rather than an option to be considered.
This paper discussed and investigated the transient stability enhancement by using a power system stabilizer PSS and static Var compensator. The study has compared the independent application of PSS and its combination with SVC using a multimachine testing system consisting of four machines and six buses in MATLAB Simulink. During three phases to ground fault on generator 1 three cases were considered to identify the differences between PSS and SVC, and their ability to fix transient stability. Firstly, at the critical clearing time the system lost the synchronism when using PSS only, and it retained synchronism when SVC was connected with the system as a controller. In a second case with a clearing time of 147 ms, the system remained stable with both PSS only and PSS with SVC; however, the result was much better when utilizing SVC for damping oscillation. In the final case, two SVCs were used, and in comparison with previous cases the results indicated improved transient stability and damping oscillation of several parameters, such as rotor angle and terminal voltage and transmission lines active power.
REFERENCES

Y. N. Yu, Electric Power System Dynamics, Academic Press, 1983.

P. M. Anderson and A. A. Fouad, Power System Control and Stability, IEEE Press, 1994.

P. W. Sauer and M. A. Pai, Power system Dynamics and Stability, Prentice Hall, 1998.

Rogers G.; Power System Oscillations, Kluwer Academic Publishers, 2000

W. Watson and G. Manchur, Experience with Supplementary Damping Signals for Generator Static Excitation Systems, IEEE Trans, PAS, Vol. 92, pp 199203,Jan 1973.

E. V. Larsen, J. S. Gasca, and J. H. Chow, Concepts for Design of FACTS Controllers to Damp Power Swings, IEEE Trans. On Power System, Vol. 10, No. 2, May 1995.

F. deMello and C. Concordia, Concepts of Synchronous Machine Stability as Affected by Excitation Control, IEEE Trans. PAS, Vol. 88, pp. 316329, 1969.

Klein, M.; Rogers, G.J.; Kundur, P., A fundamental study of inter area oscillations in power systems, IEEE Transactions on Power Systems, Volume: 6 Issue: 3, Aug. 1991, Page(s): 914 921

Klein, M., Rogers G.J., Moorty S., and Kundur, P., Analytical investigation of factors influencing power system stabilizers performance, IEEE Transactions on Energy Conversion, Volume: 7 Issue: 3, Sept. 1992, Page(s): 382 390

G. T. Tse and S. K. Tso, "Refinement of Conventional PSS Design in Multimachine System by Modal Analysis," IEEE Trans. PWRS, Vol. 8, No. 2, 1993, pp. 598605.

Y.Y. Hsu and C.Y. Hsu, Design of a ProportionalIntegral Power System Stabilizer, IEEE Trans. PWRS, Vol. 1, No. 2, pp. 4653, 1986.

Y.Y. Hsu and K.L. Liou, Design of SelfTuning PID Power System Stabilizers for Synchronous Generators, IEEE Trans. on Energy Conversion, Vol. 2, No. 3, pp. 343348

V. Samarasinghe and N. Pahalawaththa, "Damping of Multimodal Oscillations in Power Systems Using Variable Structure Control Techniques," IEE Proc. Genet. Transm. Distrib., Vol. 144, No. 3, Jan. 1997, pp. 323331.

AbdelMagid, Y.L., Abido M. A., and Mantawy A. H., Robust Tuning of Power System Stabilizers in Multimachine Power Systems, IEEE Transactions on Power Systems, Volume 15, No. 2, May 2000, pp. 735740.

A. Murdch, H. C. Sanderson, and R. Lawso; Excitation System Performance Specification to Meet Interconnection Requirements.

F. P. de Mello, P. J. Nolan, T. F. Laskowski, and J. M. Undrill, Coordinated application of stabilizers in multimachine power systems, IEEE Transactions PAS, Vol. 99, No. 3, pp: 892901, 1980.

Y. Y. Hsu and C. L. Chen, Identification of optimum location for stabilizer applications using participation factors, Pt. C, IEE Proceedings, Volume 134, No. 3, 1987, Page(s): 238244.

N. G. Hingorani, "High Power Electronics and Flexible AC Transmission System," IEEE Power Engineering Review, July 1988.

N. G. Hingorani, "FACTSFlexible AC Transmission System," Proceedings of 5th International Conference on AC and DC Power TransmissionIEE Conference Publication 345, 1991, pp. 17.

N. G. Hingorani, "Flexible AC Transmission," IEEE Spectrum, April 1993, pp. 4045.

H. F. Wang and F. J. Swift, A Unified Model for the Analysis of FACTS Devices in Damping Power System Oscillations Part I: Singlemachine Infinitebus Power Systems, IEEE Trans. PWRD, Vol. 12, No. 2, 1997, pp. 941946.

M. A. Abido and Y. L. AbdelMagid, Power System Stability Enhancement via coordinated design of PSS and FACTSBased stabilizers, Final Report of a Project Funded by FKUPM, May 2002.

X. Chen, N. Pahalawaththa, U. Annakkage, and C. Kumble, "Controlled Series Compensation for Improving the Stability of Multimachine Power Systems," IEE Proc., Pt. C, Vol. 142, 1995, pp. 361366

J. Chang and J. Chow, "Time Optimal Series Capacitor Control for Damping InterArea Modes in Interconnected Power Systems," IEEE Trans. PWRS, Vol. 12, No. 1, 1997, pp. 215221.

T. Lie, G. Shrestha, and A. Ghosh, "Design and Application Of Fuzzy Logic Control Scheme For Transient Stability Enhancement In Power System", Electric Power System Research. 1995, pp, 17 23.

P. Kundur, Power System Stability and Control, McGrawHill, 1994.

Dr.Tarlochan Kaur1 and Sandeep Kakran, "Transient Stability Improvement of Long Transmission Line System by Using SVC," International Journal of Advanced Research in Electrical, Electronics and Instrumentation Engineering, Vol. 1, Issue 4, October 2012

H. Saadat, Power System Analysis, McGrawHill, 2002.

A. A Edris, R Aapa, M H Baker, L Bohman, K Clark, Proposed terms and definitions for flexible ac transmission system (FACTS), IEEE Trans. on Power Delivery, Vol. 12, No. 4, 1997, pp. 1848 1853.

Dash. P. K, Selta Morris and Mishra. S, Design of a nonlinear Variable Controller for FACTS Devices, IEEE Transactions on Control System Technology, Vol. 12. No. 3, May 2004.

Patel, H. D,Majmudar, C,Fuzzy logic application to single machine power system stabilizer, Power Nirma University International Conference on Engineering, IEEE, Vol. 2, pp. 669 674, Dec 2011.

M. A. Abido, Analysis and assessment of STATCOM based damping stabilizers for Power system stability enhancement Electric Power System Research, 73, 177 185, 2005.

Mohan Mathur, Rajiv K. Varma ,ThyristorBased Facts Controllers for Electrical Transmission Systems, John Wiley &Sons, Inc. Publication, 2002, pp 93138.

B T Ooi, M Kazerrani, R Marcean, Z Wolanski, F D Galiana, D. Megillis, G. Joos, Midpoint sitting of FACTS devices in transmission lines, IEEE Tran. On Power Delivery, Vol. 1 No. 4, 1997, pp. 17171722.

S. M. Barakati, S. Khanmohamadi, S. H. Hosseini, Improving the Power Stability using Fuzzy Logic Controlled Static Var Compensator, the 4th Iranian Conference on Electrical Engineering, ICEE97, 1996.

Mitsubishi Electric. (2010). Power system stabilizer PSS

Samuelsson, O. (1997). Power system dampingstructural aspects of controlling active power. Lund University.

Liu, F., Yokoyama, R. , Zhou, Y. , & Wu, M. Study on Oscillation Damping Effects of Power System Stabilizer with Eigenvalue Analysis Method for the Stability of Power Systems.

E. Z. Zhou, Application of Static Var Compensators to Increase Power System Damping, IEEE Transactions on Power Systems, Vol. 8, NO. 2, 1993.

M. H. Hague, Improvement of first stability limit by utilizing full benefit of shunt FACTS devices, IEEE Transactions On Power Systems, vol. 19, no. 4, pp. 1894 1902, 2004.

Arunkumar, Priya G, Power System Stability Enhancement using FACTS Controllers, IEEE, 2012.

Claudio A. canizares, Power Flow and Transient Stability Models of FACTS Controllers for Voltage and angle Stability Studies, IEEE PES,2000.