 Open Access
 Total Downloads : 13
 Authors : D. Kanakadhurga,
 Paper ID : IJERTCONV3IS04010
 Volume & Issue : NCRTET – 2015 (Volume 3 – Issue 04)
 Published (First Online): 30072018
 ISSN (Online) : 22780181
 Publisher Name : IJERT
 License: This work is licensed under a Creative Commons Attribution 4.0 International License
UPFC with Matrix Converter using Direct Power Control
D. Kanakadhurga,
M.E, Department Of Power Systems Engineering, Parisutham Institute Of Technology, Thanjavur
Abstract In this paper presents a direct power control (DPC) for threephase matrix converters operating as unified power flow controllers (UPFCs). Matrix converters (MCs) allow the direct ac/ac power conversion without dc energy storage links; therefore, the MCbased UPFC (MCUPFC) has reduced size and cost, reduced capacitor power losses, together with higher reliability. Theoretical principles of direct power control (DPC) based on sliding mode control methods are established for an MCUPFC dynamic model including the input filter. As a result, line active and reactive power, together with ac supply reactive power, can be directly controlled by selecting an appropriate matrix converter switching state assuring good steadystate and dynamic responses. Experimental results of DPC controllers for MCUPFC show decoupled active and reactive power control, zero steadystate tracking error, and fast response times. Compared to an MCUPFC using active and reactive power linear controllers based on a modified Venturini highfrequency PWM modulator, the experimental results of the advanced DPCMC guarantee faster responses without overshoot and no steadystate error, presenting no crosscoupling in dynamic and steadystate responses.
Keywords: Ac/ac conversion advanced direct power controller, matrix converter, unified power flow controller

INTRODUCTION
Electric power flow through an alternating current transmission line is a function of the line impedance, the magnitudes of the sendingend and receivingend voltages, and the phase angle between these voltages. Essentially, the power flow is dependent on the voltage across the line impedance. Electricity market deregulation, together with growing economic, environmental, and social concerns, has increased the difficulty to burn fossil fuels, and to obtain new licenses to build transmission lines (rightsofway) and highpower facilities. This situation started the growth of decentralized electricity generation (using renewable energy resources). Unified powerflow controllers (UPFC) enable the operation of power transmission networks near their maximum ratings, by enforcing power flow through welldefined lines [2][4]. These days, UPFCs are one of the most versatile and powerful flexible ac transmission systems (FACTS) devices.
The existence of a dc capacitor bank originates additional losses, decreases the converter lifetime, and increases its
weight, cost, and volume. In the last few decades,an increasing interest in new converter types, capable of performing the same functions but with reduced storage needs, has arisen [10][12]. These converters are capable of performing the same ac/ac conversion, allowing bidirectional power flow, guaranteeing near sinusoidal input and output currents, voltages with variable amplitude, and adjustable power factor [13][14]. These minimum energy storage ac/ac converters have the capability to allow independent reactive control on the UPFC shunt and series converter sides, while guaranteeing that the active power exchanged on the UPFC series connection is always supplied/absorbed by the shunt connection. Conventional UPFC controllers do not guarantee robustness [6][8] and [11], [12]. In [10], the dependence of the matrix converter output voltage on the modulation coefficient was investigated, concluding that MCUPFC is able to control the full range of power flow. Recent nonlinear approaches [5] enabled better tuning of PI controller parameters. Still, there is room to further improve the dynamic response of UPFCs, using nonlinear robust controllers.
In the last few years, direct power control techniques have been used in many power applications, due to their simplicity and good performance [12]. In this paper, a matrix converter based UPFC is proposed, using a direct power control approach (DPCMC) based on an MCUPFC dynamic model(Section II). In order to design UPFCs, presenting robust behaviour to parameter variations and to disturbances, the proposed DPCMC control method, in Section III, is based on sliding modecontrol techniques [9], allowing the realtime selection of adequate matrix vectors to control input and output electrical power. Sliding modebased DPCMC controllers can guarantee zero steadystate errors and no overshoots, good tracking performance, and fast dynamic responses, while being simpler to implement and requiring less processing power, when compared to proportional integral (PI) linear controllers obtained from linear active and reactive power models of UPFC using a modified Venturing highfrequency PWM modulator. The dynamic and steadystate behaviour of the proposed DPCMC P, Q control method is evaluated and discussed using detailed simulations and experimental implementation (Sections IV and V). Simulation and experimental results obtained with the nonlinear DPC for
matrix converterbased UPFC technology show decoupled series active and shunt/series reactive power control, zero steadystate error tracking, and fast response times, presenting faultless dynamic and steadystate responses.

UPFC POWER SYSTEM A simplified power transmission network using the proposed matrix converter UPFC is presented in Fig. 1, Fig. 2 shows the simplified threephase equivalent circuit of the matrix UPFC transmission system model. For system modelling, the power sources and the coupling transformers are all considered ideal. Also, the matrix converter is considered ideal and represented as a controllable voltage source, with amplitude and phase . In the equivalent circuit, Vro is the load bus voltage; The DPCMC controller will treat the simplified elements as disturbances.
The active and reactive power of sending end generator
[9] are given in dq coordinates byAssuming vR0d and V s d =V d as constants and a rotating reference frame synchronized to the source Vs so that V s q = 0, active and reactive power P and Q are given by (4) and (5), respectively
Based on the desired active and reactive power (Pref, Qref ), reference currents (Idref and Iqref) can be calculated from (4) and (5) for current controllers [20]. However, allowing P, Q actual powers are sensitive to errors in the Vd, Vq values.
.
Fig 1: Transmission network with matrix converter UPFC.
Where Vs and Vr are, respectively, the sendingend and receivingend sinusoidal voltages of the Gs and G r generators feeding load Zl . The matrix converter is connected to transmission line 2, represented as a series inductance with series resistance ( L2 and R2 ), through coupling transformers.
Fig 2: Threephase equivalent circuit of the matrix UPFC and transmission line.
Considering a symmetrical and balanced threephase system and applying Kirchhoff laws to the threephase equivalent circuit (Fig. 2), the ac line currents are obtained in dq coordinates.
2.1 Matrix Converter Output Voltages and Input Currents
A diagram of the UPFC system (Fig. 3) includes the three phase shunt input transformer (with windings Ta, Tb, Tc), the threephase series output transformer (with windings TA, TB, TC ) and the threephase matrix converter, represented as an array of nine bidirectional switches Skj with turnon and turn off capability, allowing the connection of each one of three output phases directly to any one of the three input phases. The threephase (lCr) input filter is required to re establish a voltagesource boundary to the matrix converter, enabling smoth input currents.
Fig 3: Transmission network with matrix converter UPFC.
Applying dq coordinates to the input filter state variables presented in Fig. 3 and neglecting the effects of the damping resistors, the following equations are obtained:
Where Vid, Viq, Iid, Iiq represents, input voltages and input current in dq components (at the shunt transformer secondary) and Vd, Vq, Id, Iq, are matrix converter voltages and input currents in dq components respectively.

DIRECT POWER CONTROL OF MCUPFC
3.1 Direct Control of Matrix Converters Input Reactive Power
In addition, the matrix converter UPFC can be controlled to ensure a minimum or a certain desired reactive power at the
matrix converter input. Similar to the previous considerations,
since the voltage source input filter (Fig. 3) dynamics (6) has a
strong relative degree of two [25], then a suitable sliding surface SQI(eQI, t) (19) will be a linear combination of the desired reactive power error eQI= Qiref – Qi and its firstorder time derivative.
The time derivative can be approximated by a discrete time
difference, as KQi has been chosen to obtain a suitable switching frequency, since as stated before, this sliding surface needs to be quantized only in two levels (1 and +1 )
Fig 4: (a) Output currents and their corresponding sector. (b) Input current statespace vectors, when output currents are located at sector I01. The axis is represented, considering that the input voltages are located in zone V01.
To full fill a stability condition similar to (15), considering the input filter dynamics (6), (20) is obtained.
From (20), it is seen that the control input, the Iq matrix input current, must have enough amplitude to impose the sign of SQI(eQI, t) Supposing that there is enough Iq amplitude, (9) and (12) are used to establish the criteria (13) to choose the adequate matrix input current vector that imposes the needed sign of the matrix inputphase current Iq related to the outputphase currents by (9).

IfSQI(eQI, t) > 0 =>SQI(eQI, t) < 0, then select vector with current Iq<0 to increase Qi

IfSQI(eQI, t) < 0 => SQI(eQI, t) > 0, then select vector with current Iq> 0 to increase Qi .
The sliding mode is reached when vectors applied to the converter have the necessary Iq current amplitude to satisfy stability conditions, such as (15). Therefore, to choose the most adequate vector in the chosen dq reference frame, it is necessary to know the output currents location since the Iq input current depends on the output currents (Table I). Considering that the dq axis location is synchronous with the Via input voltage (i.e., reference frame depends on the Via input voltage location), the sign of the matrix reactive power Qi can be determined by knowing the location of the input voltages and the location of the output currents (Fig.4).
Table 1: Statespace vectors selection, for input voltages located at sector vi1
4.SIMULATION RESULTS
The performance of the proposed direct control system was evaluated with a detailed simulation model using the MATLAB/SIMULINK SIMPOWERSYSTEMS to represent the matrix converter, transformers, sources and transmission lines, and SIMULINK blocks to simulate the control
system. Ideal switches were considered to simulate matrix converter semiconductors minimizing simulation times.
Fig 5: Modeling circuit of the threephase matrix converter operating as a UPFC with direct power control
Fig 6: Control scheme of direct power control of the three phase matrix converter.
Fig 7: SIMULINK results of proposed UPFC (a) Output voltage, (b) Output current.
Fig 8: SIMULINK results of proposed UPFC (a) magnitude of Output voltage, (b) Magnitude of output current, (c) Real power, (d) Reactive power
Fig 9: SIMULINK results of without UPFC (a) OutputVoltage, (b) output current.
Fig 10: SIMULINK results of without UPFC (a) Magnitude of output voltage, (b) Magnitude of output current, (c) real power, (d) reactive power
Simulation results confirm the performance of the proposed controllers, showing no crosscoupling, no steadystate error (only switching ripples), and fast response times for different changes of power references. The results (Fig. 7) also show fast response without cross coupling between active and reactive power. This confirms the DPCMC robustness to input filter parameter variation, the ability to operate at low switching frequencies, and insensitivity to switching nonlinearity.
CONCLUSION
In this Presented simulation results show that active and reactive power flow can be advantageously controlled by using the proposed DPC. Results show no steadystate errors, no crosscoupling, insensitivity to nonmodeled dynamics and fast response times, thus confirming the expected performance of the presented
nonlinear DPC methodology. The obtained DPCMC results were compared to PI linear active and reactive power controllers using a modified Venturini high frequency PWM modulator. Despite showing a suitable dynamic response, the PI performance is inferior when compared to DPC. Furthermore, the PI controllers and modulator take longer times to compute.
REFERENCES

S. M. Metev and V. P. Veiko, Laser Assisted Microtechnology, 2nd ed., R. M. Osgood, Jr., Ed. Berlin, Germany: Springer Verlag, 1998.

N. Hingorani and L. Gyugyi, Understanding FACTS Concepts and Technology of Flexible AC Transmission Systems. Piscataway, NJ: IEEE Press/Wiley, 2000.J. Breckling, Ed.,

L. Gyugyi, Unified power flow control concept for flexible AC transmission systems, Proc. Inst. Elect. Eng. C, vol. 139, no. 4, Jul. 1992.

C. Schauder, L. Gyugyi, M. Lund, D. Hamai, T. Rietman, D. Torgerson, and A. Edris, Operation of the unified power flow controller (UPFC) under practical constraints, IEEE Trans. Power Del., vol. 13, no. 2, pp.630639, Apr. 1998.

F. Gao and M. Iravani, Dynamic model of a space vector modulated matrix converter, IEEE Trans. Power Del., vol. 22, no. 3, pp. 16961750, Jul. 2007.

B. Geethalakshmi and P. Dananjayan, Investigation of performance of UPFC without DC link capacitor, in Elect. Power Energy Res.. New York: Elsevier, 2008, pp. 284294, 736746.

X. Jiang, X. Fang, J. Chow, A. Edris, E. Uzunovic, M. Parisi, and L. Hopkins, A novel approach for modeling voltage sourced converterbased FACTS controllers, IEEE Trans. Power Del., vol. 23, no. 4, pp. 25912598, Oct. 2008.

R. Strzelecki, A. Noculak, H. Tunia, and K. Sozanski, UPFC with matrix converter, presented at the EPE Conf., Graz, Austria, Sep. 2001.

J. Silva and S. Pinto, , M. H. Rashid, Ed., Power Electronics Handbook, in Control Methods for Switching Power Converters, 2nd ed. New York: Academic Press/ Elsevier, 2007, ch. 34, pp. 935998.R. E. Sorace,

W. S. Levine, The Control Handbook. Boca Raton, FL: CRC, 1996,

I. Martins, J. Barros, and J. Silva, Design of cross coupling free current mode controller for UPFC series converter, in Proc. IEEE Optimization of Electrical and Electronic Equipment Conf., May 2008, pp. 209
218.pp. 911912.

H. Akagi, Y. Kanazawa, and A. Nabae, Instantaneous reactive power compensators comprising switching devices without energy storage components, IEEE Trans. Ind. Appl., vol. IA20, no. 3, pp. 625630, May/Jun. 1984.V. S. Reinhardt, and S. A. Vaughn, Highspeed digitaltoRF converter, U.S. Patent 5 668 842, Sept. 16, 1997. (2002) The IEEE website. [Online]. Available: http://www.ieee.org/

P. Wheeler, J. Rodriguez, J. Clare, L. Empringham, and A. Weinstein, Matrix converters: A technology review, IEEE Trans. Ind. Electron.,vol. 49, no. 2, pp.

276288, pr. 2002. A. Alesina and M. G. B. Venturini, Solid state power
conversion: A Fourier analysis approac to generalized transformer synthesis, IEEE Trans. Circuits Syst. , vol. CAS28, no. 4, pp. 319330, Apr. 1981.

J. Monteiro, J. Silva, S. Pinto, and J. Palma, Unified power flow controllers without DC bus: Designing controllers for the matrix converter solution, presented at the Int. Conf. Electrical Engineering, Coimbra, Portugal, 2005.