- Open Access
- Total Downloads : 13
- Authors : Vinod Sehrawat, Arvind Gupta, Gulshan Sachdeva
- Paper ID : IJERTCONV4IS03005
- Volume & Issue : RACEE – 2015 (Volume 4 – Issue 03)
- Published (First Online): 30-07-2018
- ISSN (Online) : 2278-0181
- Publisher Name : IJERT
- License: This work is licensed under a Creative Commons Attribution 4.0 International License
Review of Thermal Energy Storage Options for Solar Energy Powered Absorption Cooling Systems
1Research Scholar, Department of Mechanical Engineering,
YMCAUST, Faridabad, India
2Department of Mechanical Engineering, YMCAUST, Faridabad,
3Department of Mechanical Engineering, National Institute of Technology (NIT), Kurukshetra,
Abstract- As the world faces the global energy and environmental crisis, there is an urgent need to develop and promote environmentally benign sustainable cooling technologies. Solar absorption refrigeration is one such promising technology, and the cheapest and also widely available renewable energy that matches the cooling load requirements. Thermal applications are drawing increasing attention in the solar energy research field, due to their high performance in energy storage density and energy conversion efficiency. It is a fact that solar energy is intermittent in nature. The continuous use of solar air conditioning systems faces a challenge during operation at night due to unavailability of solar energy. This situation asks for thermal storage options. In these applications, solar collectors and thermal energy storage systems are the two core components. This paper provides a review of thermal energy storage systems and focuses on research articles in the field of storage materials, storage methods using sensible heat storage, latent heat storage, chemical storage and cascaded thermal storage systems. Various types of thermal energy storage systems are studied in terms of design criteria and material selection.
Keywords: Solar Absorption cooling, Heat energy storage, Phase change material, Cascaded thermal storage
Abbreviations: HES, heat energy storage; SHS, sensible heat storage; PCM, phase change material; COP, coefficient of performance; HTF, heat transfer fluid; LHS, latent heat storage; CS, Cold Storage; CHES, cascaded heat energy storage.
Refrigeration and air conditioning applications account for significant portion of total energy consumption in India. In recent years, these sectors have witnessed manifold growth, and have become essential not only for human comfort but also for a variety of applications, such as food preservation. Nearly 30% of all fresh produce, in developing countries like India, are lost owing to lack of cold storage facilities and unreliable grid supply . Providing thermal cooling would minimize post harvest losses. Conventional cooling technologies are energy intensive and harmful to
environment. Sustainable cooling technologies are essential to meet the increasing cooling demand in an environmentally friendly manner. Solar cooling has emerged as a viable alternative in this regard. In comparison with conventional electrically driven compression systems, substantial primary energy savings can be expected from solar cooling, thus aiding in conserving energy and preserving the environment. In solar vapour absorption cooling systems, the energy received from the solar collector is given as a heat input to the generator hence the energy has to be stored for a uniform heat supply to the generator. Another advantage of using solar energy is that the cooling demand is highest when the solar intensity is at its highest; however, the problem with solar energy is its intermittent nature and non-uniform intensity. Thermal storage therefore plays a vital role in solar based systems. Thermal storage is, therefore, critical. After the thermal energy is collected by solar collectors, it needs to be efficiently stored when later needed for a release. Thus, it becomes of great importance to design an efficient energy storage system. The following text focuses on the solar thermal energy storage, discussing its design criteria and desirable materials.
The concept of heat storage by an eco-friendly technology could help meet end-use demand economically. It enhances a fraction of the renewable energy utilization and energy efficiency of conventional systems. Energy storage has recently attracted increasing attention in many industrial and commercial applications. This paper illustrates the different types of storage methods, storage materials. The suitability of the PCM based cascaded storage system for solar cooling is also studied and presented in this paper.
The demand of solar energy based cooling systems has increased owing to certain advantages in recent times. The solar collection and storage system consists of a solar collector connected through pipes to the heat storage. Solar collectors transform solar radiation into heat and transfer that heat to the heat transfer fluid (HTF) in the collector. The hot fluid is then stored in a thermal storage unit to be subsequently utilized for various applications such as
absorption cooling systems. The performance of solar collection can be enhanced by better stratification in the storage tank. The stratification in the storage tank enhances the solar collector efficiency.
SOLAR ENERGY STORAGE METHODS
The heat energy storage (HES) system is one of the most appropriate methods of bridging the gap that exists between the demand and supply of energy. Heat can be stored in sensible/latent form, and by thermo chemical techniques.
Thermal energy storage can be achieved in the form of the
sensible heat of a solid or liquid medium,
the latent heat of a phase change substance, or
by a chemical reaction.
Various types of thermal energy storage systems like sensible heat storage, latent heat storage, chemical storage and cascaded storage are studied in terms of design criteria and material selection. The choice of the storage medium depends on the amount of energy to be stored in unit volume, or the weight of the medium, and the temperature range at which it is required for a given application. The sensible heat storage (SHS) units that use water, oil or pebble beds have very low heat capacity per unit volume. On the other hand, the latent heat storage (LHS) unit is particularly attractive, due to its high-energy storage capacity, and its isothermal behaviour during the charging and discharging process. Fig 1 shows the schematic digram of solar energy power cooling system with thermal storage .
Fig. 1 Schematic diagram of solar energy powered absorption chiler integrated with a parabolic concentrator and storage tank.
The materials used for solar thermal energy storage are classified into three main categories according to different storage mechanisms: sensible heat storage, latent heat storage and chemical heat storage (with their storage capacity in ascending order). Sensible heat storage is the most developed technology and there are a large number of low-cost materials available [2-4], but it has the lowest storage capacity which significantly increases the system size. Latent heat storage has much higher storage capacity, but poor heat transfer usually accompanies if not employing heat transfer enhancement. Chemical storage has the highest storage capacity, but the following problems restrict its application: complicated reactors needed for specific chemical reactions, weak long-term durability (reversibility) and chemical stability.
Criteria for design
There are three main aspects that need to be considered in the design of a solar thermal energy storage system: technical properties, cost effectiveness and environmental impact . Excellent technical properties are the key factors to ensure the technical feasibility of a solar thermal energy storage system. Firstly, a high thermal storage capacity (sensible heat, latent heat or chemical energy) is essential to reduce the system volume and increase the system efficiency. Secondly, a good heat transfer rate must be maintained between the heat storage material and heat transfer fluid, to ensure that thermal energy can be released/absorbed at the required speed. Thirdly, the storage material needs to have good stability to avoid chemical and mechanical degradation after a certain number of thermal cycles. The other technical properties, such as compatibility and heat loss, are listed in Table 1.
Table 1: Design criteria of a solar thermal energy storage system 
1. High thermal energy storage capacity;
2. Efficient heat transfer rate between HTF and
3. Good Mechanical and Chemical stability of storage material;
4. Compatibility between HTF, heat exchanger and/
or storage material;
5. Complete reversibility of a large number of charging and discharging cycles;
6. Low thermal losses and ease of control.
1. The cost of thermal energy storage materials;
2. The cost of the heat exchanger;
3. The cost of the space and/ or enclosure for the
thermal energy storage.
1. Operation strategy;
2. Maximum load;
3. Nominal temperature and specific enthalpy drop
4. Integration to the power plant.
Cost effectiveness determines the payoff period of the investment, and therefore is very important. The cost of a solar thermal energy storage system mainly consists of three parts : storage material, heat exchanger and land cost. Cost effectiveness is usually connected with the aforementioned technical properties, because high thermal storage capacity and excellent heat transfer performance can significantly reduce the system volume.
Apart from technical properties and cost effectiveness, there are other criteria to be considered, such as operation strategy and integration to a specific application, which are listed in Table 1.
Stratification in TES
Thermal storage is a very important link in any solar thermal supply network. Thermal stratification denotes the formation of horizontal layers of a fluid of varying temperatures with the warmer layers of fluid placed above the cooler ones. In a highly stratified storage, the return temperature to the solar collector is lowered leading to an increased efficiency of the solar collector. Collectors capitalize on low temperature heating with reduced heat loss leading to maximum heat gain from solar energy. Several studies have been carried out by
researchers on the sensible heat storage systems to improve the overall efficiency of the storage system and collection. Thermal stratification holds the key for the effective charging and discharging of the energy stored. Most of the models proposed in the literature are for simple one dimensional cases. Zurigat et al.  have carried out a survey of the stratified thermal storage one-dimensional models available in the literature. They have validated six models with the experimental data, obtained at their laboratory and from the literature, conducted under both constant and varying inlet fluid temperature conditions. The models include the fully stratified storage tank model, a modified version of this model, the viscous entrainment model and the effective diffusivity model. They have further indicated that the increase in the exergy capacity is the greatest for storages at temperatures close to the environment temperature. The exergy analysis by Jack and Wrobel  has shown that stratification delays the mixing of the incoming fluid with that in the storage tank, leading to an increase in the overall second-law efficiency and a reduction in the optimum charging time compared to the fully mixed case. The effects of different parameters and dimensionless numbers that influence and characterize stratification have been analyzed by various investigators. [9,10]. The dimensionless group analysis shows that the Richardson number is generally used as the evaluate index. Aspect ratio is one of the critical parameters to obtain stratification. Ievers and Lin  analyzed stratification in a storage tank using Fluent software, and concluded that increasing the tanks height/diameter aspect ratio, decreasing the inlet/outlet flow rates and moving the inlet/outlet to the outer extremities of the tank, results in increasing levels of thermal stratification. Andersen et al.  presented the thermal behaviour of three different modern stratifiers with fabric and rigid pipes. The effectiveness of stratifiers especially at low flow rates has been shown by Stratification improvements by PCMs have also been reported by different investigators. Cabeza et al. showed that the energy density of the hot water storage tank with stratification, increased with increasing amounts of the PCM module at the top of the tank. By means of simulation and experimental works on PCM integrated hot water stores, Mehling et al.  showed an improvement in the energy density, reheating and delay in heat loss of hot water stores.
Sensible heat storage (SHS)
In external heat storage systems, the HTF from the solar collectors will be circulated to the hot thermal storage tank to store energy for later use. An SHS system consists of a storage medium, a container and input/output ports. Containers must retain the storage material and prevent loss of thermal energy. The performance of SHS systems is influenced by factors, such as the thermal capacity of the fluid used, the operating temperature range, the design and geometry of the inlet and outlet ports, the mixing introduced during the charge and discharge cycles, thermal losses from the storage device and the degree of thermal stratification in the storage device. In sensible heat storage (SHS), thermal energy is stored by raising the temperature of a solid or liquid. Water is a most commonly used substance for thermal storage owing to its relatively high heat capacity. For cold
storage where the difference between charging and discharging usually is lower than 10Â°C the energy density of the storage is in the order of 10 kWh/m3. For heat storage this temperature difference can be greater, and the energy density larger, in the order of 40 kWh/m3 . For high temperatures the pressure in a tank containing water will have to be increased, this could be impractical and therefore other substances are often used. SHS systems utilize the heat capacity and change in temperature of the material during the process of charging and discharging. SHS characterized by temperature variation is a simpler technique, but occupies a larger volume. The amount of stored energy depends on the specific heat of the medium, temperature change and the amount of storage material. Dincer et al.  presented a detailed investigation of the availability of SHS techniques for solar thermal applications, selection criteria for SHS systems, and the economics and environmental impact of SHS systems.
Sensible heat storage materials
In sensible heat storage, thermal energy is stored during the rising or dropping of temperatures of thermal storage media, which can be either solid state or liquid state. The most commonly-used solid-state thermal storage materials, including sand-rock minerals, concrete, fire bricks and ferroalloy materials.
K) 7.0 W/(m K) for sand-rock minerals, concrete and fire bricks, 37.0 W/(m K) 40.0 W/(m K) for ferroalloy materials. The materials shown in Table 3 are all low-cost ranging from Rs. 30/kg Rs. 300/kg. The only disadvantage is their heat capacities being rather low, ranging from 0.56 kJ/kg to 1.3 kJ/kg, which can make the storage unit unrealistically large. Another method of SHS is the use of a packed bed of solids for storing thermal energy. The packed bed provides an effective means of energy storage for many systems and has been satisfactorily employed for various applications. Beasly and Clark  summarized the status of the SHS modeling of packed beds, including numerical investigations. Saez and Mcoy , Torab and Beasley  and Sozen  studied the performance of packed bed SHS systems using one- dimensional separate phases models. Table 2 shows the main characteristics of the most commonly-used solid-state thermal storage materials .
Table 2 Solid-state sensible heat storage materials. 
Working Temperatur e oC
Density [kg/m3 ]
Thermal Conductiv ity W/mK
Specifi c heat kJ/kg
Specific heat kWht/m3o C
In a rock-bed-storage rocks, kept in a container, are used as substance. Air is blown through the container to charge and discharge it. This can be practical if the heat source as well as the heat demand is in form of hot air. It seems like it could be used as a cool storage as well. Energy losses from a sensible heat storage are in form of heat flow the storage to the cooler or warmer ambient environment outside the storage. This increases as the temperature difference increases. If additional heat exchangers are needed (to reduce the amount of antifreeze for example) there are also temperature losses. For large-scale storage applications filled rooms below surface of the ground or bore holes into the bedrock can be used. (Note that a single bore hole will not do well as a storage because of extensive heat leakage. For a bore hole storage to work a group consisting of several bore holes is needed). The temperature requirement for the generator will be different depending on the type of vapor absorption system (half/single/double/triple effect). However, for all these systems, heat has to be supplied within a narrow operating temperature range of 510Â°C for better performance. Hence, storing a large quantity of heat within a narrow temperature range in a sensible heat form requires a large volume storage tank. This type of sensible heat storage tank may be useful only for the purpose of providing uniform heat flux to the generator, irrespective of fluctuations in solar radiation intensity. Sensible heat storage is not capable of providing a large quantity of heat required for the generator during non-sunshine hours. Liquid-state thermal energy storage materials are shown in Table 3 , including oils, liquid sodium and inorganic molten salts. Liquid-state thermal energy storage materials include oils, liquid sodium and inorganic molten salts.
Working Temperatur e
Densit y [kg/m3
Thermal Conductivit y W/mK
Specifi c heat kJ/kg
Specific heat kWht/m
Table 3 Molten salts and high temperature oils .
Oils have rather high vapour pressure  which causes serious safety issues due to requiring an airtight system. Liquid sodium has a thermal conductivity as high as 71.0 W/(m K); however, it is highly unstable in chemical reactivity, therefore incurring much more cost by adopting extra safety measures. Molten salts are regarded as the ideal materials [2-4,6] for use in solar power plant because of their excellent thermal stability under high temperatures, low
vapour pressure, low viscosity, high thermal conductivities, non-flammability and non-toxicity.
Zhao and Wu  reported a serial of novel ternary salt mixtures with ultra-low melting temperatures of 76Â°C, 78Â°C and 80Â°C, which are all below 100Â°C so that the system unfreezing becomes much easier. Their salt mixtures consisting of KNO3, LiNO3 and Ca(NO3)2 showed much lower viscosities (more than 80%) than synthetic oils and commercial molten salts. Their salt mixtures were also found to have good chemical stability under high temperatures (500Â°C). Such eutectic salts with melting temperatures below 100Â°C were also reported by Wang et al.  recently. They found a novel quaternary eutectic salt with its melting temperature as low as 99Â°C. The common advantage of sensible heat storage is its low cost, ranging from Rs. 30/kg Rs. 300/kg compared to the high cost of latent heat storage which usually ranges from Rs. 260/kg Rs. 20450/kg .
Latent heat storage (LHS)
Latent heat storage (LHS) systems are capable of storing a large quantity of heat in smaller volumes and have isothermal behaviour during the heat retrieval process. Hence, the problem encountered in sensible heat storage is avoided in a latent heat storage system that can supply heat to the generator at an approximately constant temperature for a longer duration even during non-sunshine hours. The latent heat storage (LHS) is based on heat absorption or release when a phase change material (PCM) undergoes a phase change. The latent heat storage by PCM in comparison with SHS, possesses a greater density of stored energy and operates in a narrower operational temperature range. Zalba et al.  have reviewed various aspects of latent heat storage systems, such as PCMs heat transfer and applications. PCMs are advantageous for the dynamic and static storage of heat energy as they absorb and release large amounts of energy at specific temperatures. However, the low thermal conductivity of PCMs and the loses associated with thermal storage, are its disadvantages. A detailed description on various aspects of thermal storage systems are presented by Dincer et al. . A good understanding of the heat transfer processes involved in an LHTS unit is essential for accurately predicting the thermal performance of the system, and for avoiding a costly system design. Solidification and melting are important phenomena in thermal storage applications.
Latent heat storage materials
Phase change materials (PCMs) can store/release a large amount of heat when reforming their phase structures during melting/solidification or gasification/liquefaction processes. Since the phase-transition enthalpy of PCMs are usually much higher (100-200 times as shown in Table 4) than sensible heat, latent heat storage has much higher storage density than sensible heat storage.
Table 4 Commercial PCMs materials, inorganic salts and eutectics [6, 2].
Phase change temperatu re
Density (kg/ m3)
Thermal Conducti vity (W/m K)
Laten t heat (kJ/k g)
Latent heat (MJ/ m3
These materials have phase change temperatures ranging from 100 to 897Â°C, and latent heat ranging from 124 to 560 kJ/kg. Unlike sensible heat storage in which materials have a large temperature rise/drop when storing/releasing thermal energy, latent heat storage can work in a nearly isothermal way, due to the phase change mechanism. This makes latent heat storage favourable for those applications which require strict working temperatures. However, the main disadvantage of latent heat storage is its low thermal conductivities, which mostly fall into the range of 0.2 W/(m K) to 0.7 W/(m K), and therefore relative heat transfer enhancement technologies must be adopted .
Chemical storage uses the same principles as sorption heat pumps. In the closed liquid absorption cycle, storage can be obtained by storing strong or even crystallized solution in (or in connection with) the generator and absorber and refrigerant in the condenser (or in a separate tank). In the solid sorption cycle, storage is obtained by simply holding the process after water has been desorbed from the sorbent. In the open absorption and the desiccant systems, storage can be accomplished in the same way with the exception that no refrigerant needs to be stored. Since the system is still essentially a heat pump the storage cannot be discharged without either input or rejection of heat. When heat is discharged, low-grade heat (low temperature heat) must be provided to an evaporator to create steam that can be absorbed or adsorbed. When cooling capacity is discharged, heat from the absorber/adsorber must be rejected. Rejecting heat should not be a problem when the storage (for example) is used for compensating for lack of solar radiation in a solar air conditioning (because of clouds or during the night). However, if used to cover peak demand due to high solar insolation, high outdoor temperature and high outdoor humidity, heat rejection could be a serious problem. When the storage is being charged, heat needs to be rejected from the condenser; this could also be problematic in a solar air conditioning system since at the time that the energy supply from the solar collectors to charge is most abundant, during peak noon, heat rejection is, as mentioned above, not uncomplicated. A suggested solution for these problems, to use a pond as heat sink, actually is the same as having it
connected to a sensible cold storage. Thereby a kind of hybrid storage has been created. The need for heat rejection at storage is not present in an open system.
Collier  suggested that open absorption systems are more suitable for chemical storage than a closed, because in an open absorption system the generator is at atmospheric pressure while in a close system it is at subatmospheric pressure. Thus the strong solution in an open system can be stored in a simple tank while strong solution in a closed system would have to be stored in large pressure vessels. However, introducing an additional pump to pump the strong solution from the sub-pressure in the system to a storage tank at atmospheric pressure could easily solve this disadvantage for the closed system. The total lift of this additional pump and the systems normal solution pump together would then be the same as the pressure lift required by the single solution pump in an open system. Adsorption of water in silica gel or on zeolites is a demonstrated technology leading to energy densities based on the volume of adsorbent in the order of 150 kWh/m3. Reactions involving water and solid salts have been tested but have not yet reached commercial level . Losses in a chemical storage are connected to charging and discharging the storage. Unlike the sensible and latent storage there are no continues heat losses when not charged and discharged. The system could therefore be charged and then left charged for extended times without any energy being lost. A disadvantage with chemical storage is that the sorptive substances seem to be rather expensive, and the storage is also rather complex compared to a sensible or latent storage. This could make it economically unattractive.
Table 5 Materials used as chemical energy storage media.
Temperature range (Â°C)
Enthalpy change during chemical
Iron carbonate 
Metal hydrides 
Hydroxides, e.g. 
Calcium carbonate[27, 29]
COLD STORAGE (CS)
Storage of cold produced during sunshine hours in a cool thermal storage tank, either in a sensible heat form or in a latent heat form is yet another option of storing energy. Cold storage (CS) has recently attracted increasing interest in industrial refrigeration applications, such as process cooling, food preservation and building air conditioning systems. CS appears to be one of the most appropriate methods for correcting the mismatch that occurs between the supply and demand of energy. Cold energy storage requires a better insulation tank as the energy available in the cool state is expensive, compared to the heat available in a hot storage tank.
Sensible heat chilled water storage systems utilizing stratification tanks were studied by Tran et al.  and Musser and Bahnfleth . Nelson et al.  have pointed
out that te percent cold recoverable in a discharge cycle increases with increasing initial temperature difference, aspect ratio and flow rate. Karim  has indicated that partial discharging in one discharge cycle involves a relatively longer residence time of cool water in storage that leads to a significant decrease in thermal efficiency, as the temperature of the chilled water in the tank increases because of heat conduction through the walls. Hence, for any practical requirements the storage system should be designed with several tanks, so that based on the cooling requirement, the required number of tanks can be charged and discharged. Storing energy in the latent form has its own advantage, compared to the energy storage in a sensible heat form. Fukusako and Yamada  have reviewed the transport phenomena observed during the melting of the PCM inside ducts and over external bodies. Ermis et al.  have proposed a feed-forward back-propagation artificial neural network algorithm, for the heat transfer analysis of the phase change process in a finned tube latent heat thermal energy storage system. They have compared the performance of the model with experimental data and the numerical results obtained through heat transfer analysis with ethyl alcohol as the HTF and pure water as the PCM. For a similar PCMHTF combination, Erek and Dincer et al.  have dwelt on the entropy and exergy efficiency analysis of a shell and tube latent heat storage system. Ezan et al.  investigated the energetic and exergetic performances of a shell and tube latent energy storage system using water as PCM and ethylene glycol as the HTF. They concluded that for the charging period, the exergetic efficiency increased with the increase in the inlet temperature and the flow rate. For the discharging period, irreversibility increased as the temperature difference between the melting temperature of the PCM and the inlet temperature of the HTF increased, and hence the exergy efficiency increased. Bedecarrats et al.  presented the experimental results of the charge and discharge modes of LHTS for air conditioning/refrigeration applications using PCM encapsulated spherical capsules. The improvement in the heat transfer rates in storage units employing multiple PCMs, inserting a metal matrix into the PCM, using PCM dispersed with high conductivity particles, and micro-encapsulation of the PCM, have been studied and reported by various researchers. Velraj et al.  carried out investigations in cold storage integrated with a large air conditioning system located at Chennai, India. They have concluded that the integration of CS integrated systems in applications such as food preservation, would prove beneficial. Cheralathan et al.  investigated the performance of an industrial refrigeration system integrated with CS. The authors have indicated significant savings in capital and operating cost, in thermal storage integrated systems. The size of the PCM based CS system was also considerably reduced when compared with that of a chilled water system. Wu et al.  investigated the effects of the flow rate, inlet temperature of the HTF, porosity of the packed bed consisting of n-tetradecane, and the size of the capsules on the dynamic performance of the cool thermal storage system during the charging and discharging process. Fang et al.  reported better performance and stable charging and discharging periods of an experimental cool
storage air-conditioning system, with a spherical capsules packed bed. The numerical heat transfer analysis of an encapsulated ice thermal energy storage system with a variable heat transfer coefficient by Erek and Dincer , has revealed that the solidification process is chiefly governed by the magnitude of the Stefan number, capsule diameter and capsule row number.
A. Chemical heat storage materials
Special chemicals can absorb/release a large amount of thermal energy when they break/form certain chemical bonds during endothermal/exothermal reactions. Based on such characteristics, the storage method making use of chemical heat has been invented. Suitable materials for chemical heat storage can be organic or inorganic, as long as their reversible chemical reactions involve absorbing/ releasing a large amount of heat. When designing a chemical storage system, three basic criteria need to be considered: excellent chemical reversibility, large chemical enthalpy change and simple reaction conditions (reactions cannot be too complicated to be realised). Table 5 gives a list of potential materials for chemical heat storage, most of which have an enthalpy change of 3.6 GJ/m3 4.4 GJ/m3. As seen from Table 4 and Table 5, latent heat storage has storage densities in the order of MJ/m3, whilst chemical heat storage has much higher storage densities in the order of GJ/m3. However, chemical storage has not yet been extensively researched, and its application is limited due to the following problems: complicated reactors needed for specific chemical reactions, weak long-term durability (reversibility) and chemical stability.
Fig. 2. Solar heating/cooling system with an absorption chiller and latent heat storage in the cooling mode .
Helm et al.  have described the operation of an absorption cooling system, that involves latent heat storage supporting the heat rejection of the absorption chiller, in conjunction with a dry cooling system as shown in Fig. 2. They have indicated low temperature latent heat storage together with a dry air cooler, as a promising alternative to the conventional
wet cooling tower, as it substantially reduces the over-sizing of the solar collector system. Berlitz et al.  have introduced one more concept of storing a cool refrigerant internally in the absorption chiller system, in order to ensure a continuous supply of cool energy with minimal dependence on an external heat source to normalize fluctuation in the availability of solar energy. Rizza  has observed that the storage volumetric efficiency for the LiBr/H2O system is greater than or comparable to, that of a thermal storage system based on waterice, and that it far exceeds the value of a thermal storage system based on liquid water.
CASCADED HEAT ENERGY STORAGE (CHES)
The main advantage of latent heat storage over sensible heat storage is the high storage density within a small temperature band. For the small temperature difference covering the phase change, there is a factor of three between the heat stored in the latent heat storage system and the sensible heat storage system. For a larger temperature difference, the advantage of the latent heat storage shrinks to 6:4 = 1.5, so that there is no reason to prefer a latent heat storage system to a sensible heat storage system. A cascaded storage system offers vast potential for the improvement of a solar cooling system performance. In a cascaded storage system, PCMs with different melting temperatures are arranged in a series to store heat in different temperatures. In comparison with a conventional single PCM based storage system, a cascaded multiple PCM based storage system would improve solar collecting efficiency as the lower temperature at the bottom of the tank is connected to the inlet of the solar collector. The numerical results from the parametric study investigated by Shaikh and Lafdi  indicated that the total energy charged rate can be significantly enhanced by using composite PCMs as compared to the single PCM. Gong and Mujumdar  proposed a solar receiver store consisting of multiple PCMs and found that the fluctuation of the outlet temperature of the HTF can be greatly dampened by using multiple PCMs compared with a single PCM.
Deng et al.  have outlined the need for R&D in the cascade utilization of thermal energy in combined cooling, heating and power systems. Gordon and Ng  have proposed a high efficiency solar cooling involving a thermodynamic cascade that comprises of solar-fired gas micro-turbine producing electricity that drives a mechanical chiller, wit the turbine heat rejection running an absorption chiller. Depending on the stored temperature level and the temperature required in the generator of an absorption cycle, different solar absorption cooling equipments can be employed to facilitate the use of stored heat. Multiple effect absorption chillers have a higher COP but can operate only at high temperatures. Though half and single effect absorption cooling systems have lower COPs, they are advantageous in utilizing the stored heat at a low temperature. A combination of the multiple effect and half/single effect can thus be chosen, based on stored temperature availability. Technical considerations favour such a combination of thermally driven cooling technologies with a multiple PCM based storage
system. However, the cost and space requirements might be a limiting factor. The thermo-economic optimization of such a system would lead to a prudent design, optimization and selection of equipments. However, its economic viability needs further study.
Mehling and Cabeza  suggested that the use of a cascaded arrangement of multiple PCMs with different melting temperatures should solve the above problem. Figure 3(b) shows a typical three-stage cascaded storage system: the PCM I with the lowest melting temperature is heated from T1 to T2, the PCM II with the medium melting temperature is heated from T2 to T3, and the PCM III with the highest melting temperature is heated from T3 to the maximum temperature. Using such a cascaded storage system, the difference of the stored energy between cascaded latent heat storage and single sensible heat storage is 10:4 = 2.5.
Fig. 3. Comparison of stored heat between sensible heat storage and latent heat storage : (a) With a single PCM; (b) With cascaded latent heat storage.
Another reason for using cascaded thermal energy storage is illustrated as following. A very common practical situation is that the charging and discharging time is usually limited and the heat needs to be absorbed or released quickly. When charging a storage system with only a single-stage PCM, the heat transfer fluid rapidly transfers heat to the PCM. The temperature of the heat transfer fluid therefore reduces, which reduces the temperature difference between the PCM and heat transfer fluid  and leads to poor heat transfer at the end of the storage. As a result, the PCM is melted rapidly at the entrance part where the heat transfer fluid enters the storage, but the PCM is melted more slowly at the end of the storage where the heat transfer fluid outflows. For the discharging process, the problem is that the PCM at the end of the storage might not be used for latent heat storage as the temperature of heat transfer fluid rises. By using cascaded thermal energy storage, such problems can be all solved.
Figure 4 gives a comparison between a single-stage PCM system and a five-stage cascaded PCM system [2, 52]. For charging process, a PCM with a lower melting temperature
can be placed at the end of the heat exchanger, so that the temperature difference can be large enough to ensure all PCMs to be melted. The cascaded storage system also works efficiently for discharging process. Michels and Pitz-Paal investigated cascaded latent heat storage for parabolic trough solar power plants, and they found that a higher portion of the PCM can run through the phase change process and a more uniform heat transfer fluid outlet temperature was achieved during the discharging process than in the traditional single stage storage system. As the research by Michels and Pitz-Paal suggested, Cascaded Heat Energy Storage (CHES) was found to have higher energy utilisation efficiency than the traditional Single-stage Thermal Energy Storage (STES).
Fig 4. Comparison between a single-stage storage system and a five-stage cascaded storage system
Very recently, Tian and Zhao  examined and compared STES, CHES and their newly-proposed Metal Foam-enhanced Cascaded Thermal Energy Storage (MF- CHES). Their research showed that the CHES can not only achieve higher energy efficiency (up to 30%) than STES but can also achieve higher exergy efficiency (up to 23%) than STES. Other findings from their research are: Firstly, MF- CHES can further increase heat transfer rate of CHES by 27 times, depending on the properties of the metal-foam samples used (higher pore density and lower porosity can achieve a better performance). Secondly, MF-CHES cannot improve exergy efficiency of CHES, but can help CHES to finish melting more quickly by having higher heat transfer rates (melting time reduced by 6787%). Thirdly, exergy transfer rate of CHES is further increased by 27 times if MF-CHES is used.
It can be concluded from this review that thermal energy storage is essential in the continuous working of the solar energy powered absorption cooling system, in order to correct the intermittent nature of the solar energy. Thermal storage integrated solar cooling systems increase the cooling availability, capacity and improve the overall performance. Absorption chillers have gained considerable attention among researchers. The materials used for high-temperature thermal energy storage systems have been compared, and a comparison between different categories of thermal storage systems has been presented. Molten salts with excellent properties are considered to be the ideal materials for high-
temperature thermal storage applications. Heat transfer enhancement is also essential to overcome the poor heat transfer in these applications. For this purpose, graphite composites and metal foams are found to be the ideal materials. More research and development on enhanced solar cooling techniques coupled with a simpler, energy efficient and cost effective thermal storage system, possessing higher energy density would lead to economic competitiveness. It would also assist in the further development of affordable thermal storage systems and increase the market penetration of solar cooling.
L.A. Chidambaram, A.S. Ramana, G. Kamaraj, R. Velraj. Review of solar cooling methods and thermal storage options. Renewable and Sustainable Energy Reviews 2011;15:3220-28.
Pilkington Solar International GmbH. Survey of thermal storage for parabolic trough power plants. NREL Report, NREL/SR-550-27925; 2000.
Zhao CY, Wu ZG. Thermal property characterization of a low melting- temperature ternary nitrate salt mixture for thermal energy storage systems. Sol. Energ. Mat. Sol. C.2011;95:33413346.
Zhao CY, Zhou D, Wu ZG. Hear transfer enhancement of phase change materials (PCMs) in low and high temperature thermal storage by using porous materials. In: Proceedings of the 14th International Heat Transfer Conference (IHTC-14); Washington DC, USA, 2010.
Tian, Yuan and Zhao, Chang-Ying. (2013) A review of solar collectors and thermal energy storage in solar thermal applications. Applied Energy,104, 538-53.
Gil A, Medrano M, Martorell I, LÃ¡zaro A, Dolado P, Zalba B, Cabeza LF. State of the art on high temperature thermal energy storage for power generation. Part 1 concepts, materials and modellization. Renew. Sust. Energ. Rev. 2010;14:3155.
Zurigat YH, Maloney KJ, Ghajar AJ. A comparison study of one- dimensional models for stratified thermal storage tanks. Journal of Solar Energy Engineering 1989;111:20410.
Jack MW, Wrobel Jan. Thermodynamic optimization of a stratified thermal storage device. Applied Thermal Engineering 2009;29:23449.
Castell A, Medrano M, Sole C, Cabeza LF. Dimensionless numbers used to characterize stratification in water tanks for discharging at low flow rates. Renewable Energy 2010;35(10):21929.
Haller MY, Cruickshank CA, Streicher W, Harrison SJ, Andersen E, Furbo S. Methods to determine stratification efficiency of thermal energy storage processes review and theoretical comparison. Solar Energy 2009;83:184760.
Ievers S, Lin W. Numerical simulation of three-dimensional flow dynamics in a hot water storage tank. Applied Energy 2009;86:2604 14.
Andersen E, Furbo S, Fan Jianhua. Multilayer fabric stratification pipes for solar tanks. Solar Energy 2007;81(10):121926.
Cabeza LF, Ibanez M, Sole C, Roca J, Nogues M. Experimentation with a water tank including a PCM module. Solar Energy Materials and Solar Cells 2006;90(9):127382.
Mehling H, Cabeza LF, Hippeli S, Hiebler S. PCM-module to improve hot water heat stores with stratification. Renewable Energy 2003;28:699711.
Setterwall F., Bales C. Bolin G (2003) Thermo chemical Accumulator- TCA Preprint from Proc. IEES 2003 World Congress: GÃ¶teborg,
Dincer I, Dost S, Li X. Performance analysis of sensible heat storage systems for thermal applications. International Journal of Energy Research 1997;21(12):115771.
Beasley DE, Clark JA. Transient response of a packed bed for thermal energy storage. International Journal of Heat and Mass Transfer 1984;27(9):165969.
Saez AE, McCoy BJ. Dynamic response of a packed bed thermal storage system a model for solar air heating. Solar Energy 1982;29(3):2016.
Torab H, Beasley DE. Optimization of a packed bed thermal energy
storage unit. Journal of Solar Energy Engineering 1987;109:1705.
Sozen M, Vafai K, Kennedy KA. Thermal charging and discharging of sensible and latent heat storage packed beds. AIAA Journal of Thermophysics 1991;5(4):6235.
Wang T, Mantha D, Reddy RG. Novel low melting point quaternary eutectic system for solar thermal energy storage. Appl. Energ. 2012; correct proof, in press.
Zalba B, Marn JM, Cabeza LF, Mehling H. Review on thermal energy storage with phase change: materials, heat transfer analysis and applications. Applied Thermal Engineering 2003;23:25183.
Dincer I, Marc Rosen A. Thermal energy storage: systems and applications. John Wiley & sons Ltd; 2002.
Zhao CY, Lu W, Tian Y. Heat transfer enhancement for thermal energy storage using metal foams embedded within phase change materials (PCMs). Sol. Energy 2010;84:1402-12.
Coillier R.K.(1979) The analysis and simulation of an open cycle absorption refrigeration cycle Solar energy Vol. 23 pp. 357-366 ISSN:0038-092x.
Shiizaki S, Nagashimga I, Iwata K, Hosoda T, Kameyama H. Development of plate fin reactor for heat recovery system using methanol decomposition. In: Proceedings of the 8th International Conference on Thermal Energy Storage (Terrastock 2000); Stuttgart, Germany, 2000.
Hahne E. Thermal energy storage some view on some problems. In: Proceedings of the 8th International Heat Transfer Conference San Francisco; USA, 1986.
Lovegrove K. A solar driven ammonia based thermochemical energy storage system. In: Proceedings of ISES99 Solar world congress Jerusalem; Israel, 1999.
Kubota M, Yokoyama K, Watanabe F, Hasatani M. Heat releasing characteristics of CaO/CaCO3 reaction in a packed bed for high temperature heat storage and temperature up-grading. In: Proceedings of the 8th International Conference on Thermal Energy Storage (Terrastock 2000); Stuttgart, Germany, 2000.
Tran N, Kreider J, Brothers P. Field measurements of chilled water storage thermal performance. ASHRAE Transactions 1989;95(1):110612.
Musser A, Bahnfleth WP. Field-measured performance of four full- scale cylindrical stratified chilled-water thermal storage tanks. ASHRAE Transaction 1998;105(2):21830.
Nelson JEB, Balakrishnan AR, Srinivasa Murthy S. Transient analysis of energy storage in a thermally stratified water tank. International Journal of Energy Research 1998;22:86783.
Karim MA. Performance evaluation of a stratified chilled-water thermal storage system, world academy of science. Engineering and Technology Journal: Mechanical and Aerospace Engineering 2010;5(1):1826.
Fukusako S, Yamada M. Melting heat transfer inside ducts and over external bodies. Experimental Thermal and Fluid Science 1999;19:93 117.
Ermis K, Erek A, Dincer I. Heat transfer analysis of phase change process in a finned-tube thermal energy storage system using artificial neural network. International Journal of Heat and Mass Transfer 2007;50:316375.
Erek A, Dincer I. An approach to entropy analysis of a latent heat storage module. International Journal of Thermal Sciences 2008;47:107785.
Ezan MA, Ozdogan M, Gunerhan H, Erek Aytunc, Hepbasli Arif. Energetic and exergetic analysis and assessment of a thermal energy storage (TES) unit for building applications. Energy and Buildings 2010;42:1896901.
Bedecarrats JP, Strub F, Falcon B, Dumas JP. Phase-change thermal energy storage using spherical capsules: performance of a test plant. International Journal of Refrigeration 1996;19(3):18796. J.P.
Velraj R, Cheralathan M, Renganarayanan S. Energy management through encapsulated PCM based storage system for large building air conditioning application. International Energy Journal 2006;7(4):253 9.
Cheralathan M, Velraj R, Renganarayanan S. Performance analysis on industrial refrigeration system integrated with encapsulated PCM-based cool thermal energy storage system. International Journal of Energy Research 2007;31:1398413.
Wu S, Fang G, Xu Liu. Thermal performance simulations of a packed bed cool thermal energy storage system using n-tetradecane as phase change material. International Journal of Thermal Sciences 2010;49:175262.
Fang G, Wu S, Xu Liu. Experimental study on cool storage air- conditioning system with spherical capsules packed bed. Energy and Buildings 2010;42:105662.
Erek A, Dincer I. Numerical heat transfer analysis of encapsulated ice thermal energy storage system with variable heat transfer coefficient in downstream. International Journal of Heat and Mass Transfer 2009;52(34):8519.
Helm M, Keil C, Hiebler S, Mehling H, Schweigler C. Solar heating and cooling system with absorption chiller and low temperature latent heat storage: energetic performance and operational experience. International Journal of Refrigeration 2009;32:596606.
Berlitz T, Lemke N, Satzger P, Ziegler F. Cooling machine with integrated cold storage. International Journal of Refrigeration 1998;21(2):15761.
Rizza JJ. Lithium bromide and water thermal storage system. ASME Journal of Solar Energy Engineering 1988;110:32734.
Shaikh S, Lafdi K. Effect of multiple phase change materials (PCMs) slab configurations on thermal energy storage. Energy Conversion and Management 2006;47:210317.
Gong ZX, Mujumdar AS. Thermodynamic optimization of the thermal process in energy storage using multiple phase change materials. Applied Thermal Engineering 1997;17:106783.
Deng J, Wang RZ, Han GY. A review of thermally activated cooling technologies for combined cooling, heating and power systems. Progress in Energy and Combustion Science 2010:132.
Gordon JM, Ng KC. High-efficiency solar cooling. Solar Energy 2000;68(1):2331.
Mehling H, Cabeza LF. Heat and cold storage with PCM: Chapter 6 Integration of active storages into systems, p. 191189; Berlin:
Springer Publication Corporation, 2008.
Medrano M, Gil A, Martorell I, Potou X, Cabeza LF. State of the art on hightemperature thermal energy storage for power generation. Part 2 Case studies. Renew. Sust. Energ. Rev. 2010;14:5672.
Michelsa H, Pitz-Paal R. Cascaded latent heat storage for parabolic trough solar power plants. Sol. Energy 2007;81:829837.
Tian Y, Zhao CY. A thermal and exergetic analysis of Metal Foam- enhanced Cascaded thermal Energy storage (MF-CTES). Int. J. Heat Mass Tran. 2013;58:869.