- Open Access
- Authors : Vandana Bakolia , S. N. Joshi
- Paper ID : IJERTV9IS080181
- Volume & Issue : Volume 09, Issue 08 (August 2020)
- Published (First Online): 22-08-2020
- ISSN (Online) : 2278-0181
- Publisher Name : IJERT
- License: This work is licensed under a Creative Commons Attribution 4.0 International License
Design and Analysis of Fuzzy Logic based Power System Stabilizer
Tech Scholar, Power System, Govt. Women Engineering College,
S. N. Joshi
Assistant Professor, EE Dept Govt. Women Engineering College,
Abstract This paper presents a new fuzzy logic controller as power system stabilizer being used for stability enhancement and improving the dynamic response of the power system under faulty conditions. Power system stabilizer is added to the generator excitation system to enhance the damping during low frequency oscillations. In order to improve the stability of the power system, acceleration and rotor speed deviation of the synchronous machine are taken as input of fuzzy logic controller. These variables produce an effect on controlling the damping of generator mechanical shaft. In this paper proposed control power system stabilizer is being compared with the conventional power system stabilizer and multi brand power system stabilizer. Proposed control techniques are simulated over the IEEE 39 bus system under different conditions (with noise, without noise). Simulations of the control technique are carried out on MATLAB/SIMULINK tool.
Keywords Power System Stabilizer (PSS), Fuzzy Logic power system stabilizer (FL-PSS), Multi-Brand Power System Stabilizer (MB-PSS), Fuzzy Logic Controller (FLC).
Electrical power system is basically a dynamic system. In this type of system disturbances occur constantly which causes generator angle and voltage to change. When disturbances are removed, steady state operating condition is attained .
In todays modern time, all synchronous machines operate in synchronism and deliver power to load. When load of the generator changes, fast or slow down of synchronous generator rotor occur which in turn changes the frequency of 0.7 to 2Hz. However, PSS associated with generator is an essential control to bring the frequency back to normal value. It also improves the transmission capacity and stability of the power system .
PSS are the most important devices to damp out p low frequency oscillations caused by various disturbances like fault, load changes. Stability of electrical power system is improved by using suitable design and tuning of the PSS which improves the damping frequency oscillation. PSS is added to the generator excitation system in order to provide a supplementary signal to excitation system and to extend the stability limit by modulating generator excitation which provides the positive damping torque to power swing mode[14,9,11].
One of the most occurring stability problems arising from large electric power system is the low frequency
oscillations of interconnected power systems. These oscillations can be removed by connecting PSS with the associated generator. In this paper, concept of 3 phase fault is introduced in the bus system having 10 distributed generators (DG) units. Ideally, different types of tuned PSS are used for frequency control methods of bus system to minimize the impact of stability enhancement of complete power system. Here, the time domain reaction with different cases namely without PSS and with different type of PSS are being investigated for synchronous machine and are also compared with the proposed controller by Fuzzy logic based PSS controller [9-14]. This comparison of control technique will demonstrate that the proposed technique have lower setting time and more robustness against parameter variations and external disturbances than the conventional controller which is shown in simulation result using IEEE 39 test bus system .It also presents the effect of 3 phase fault on the network using proposed controlling PSS methods.
In this paper, MATLAB/simulation software is used to test the proposed PSS methods using IEEE 39 bus system. This system is employed to verify and demonstrate the superiority of the proposed PSS verses the conventional PSS. Several simulation conditions have been illustrated, compared and evaluated in this paper.
The objective of this paper is the frequency control of IEEE 39 test system using fuzzy logic based PSS and compare with the proposed technique. This paper is designed in the following manner: The section (ii) provides an overview of conventional PSS, section (iii) states the theory of proposed method and section (iv) compares the different type of PSS used in this paper. Finally the conclusion is being given.
MODELLING OF 39 BUS SYSTEM
In this paper, MATLAB/SIMULINK software is being used to test the proposed PSS methods using IEEE 39 bus test system. It consist of 10 generators, 19 loads, and 39 buses.
paper, we study and simulate conventional PSS (Delta w PSS, delta Pa PSS), MB-PSS and Fuzzy logic based PSS.
Conventional Power System Stabilizer
The basic function of Power System Stabilizer is used to add damping to the rotor oscillations of the synchronous machine (DG) by controlling its excitation. The
3 18 17 9
1 15 16
disturbances (fault, noise, etc.) occurring in power system induces electromechanical oscillations of the synchronous generators. These electromechanical oscillations also called as power swings, must be effectively damped to maintain
9 4 14
the stability of the power system. The output signal of PSS is used as an additional input (vstab) to the Excitation System. The PSS input signal can be either the acceleration power, Pa = Pm – Peo (the difference between the
AREA -2 7
mechanical power and the electrical power), or its (dw) speed deviation [9,11].
(1 sT w)
(1 sT w)
A complete block diagram of the PSS for non linear system is shown in figure 3. it consist of a washout high pass filter, a low pass filter, a gain, a phase compensator, and an output limiter.
(1 sT 3)
Fig 1. 39 bus 10 machine test system
(1 sT2 )
(1 sT4 )
machine New-England Power System is shown in figure 1. For simplification, this system was divided in three areas (AREA 1, AREA 2, and AREA 3). The AREA 1 consist of machine 3 and machine 2. Machine 1 is taken as reference bus and the value of speed and rotor angle deviation is zero. So, the interaction between M2 and M3 is defined as local-area mode in AREA 1. The interaction between machines (M2 and M3) in the Area 1 to machines in other areas (M10 and M8) is called as inter-area mode [15,16]. Performance of 39 bus system in case of 3-phase fault is applied close to the bus 17 and 16, result shown in section IV.
Figure 2 shows the generalized model of synchronous generator with different type of PSS associated model.
Washout Lead-lag Lead-lag
Fig 3. Power System Stabilizers
Gain (K) is the amount of damping produced by the PSS. Washout high pass filter (W) subtract low frequency signal present in dw.
Phase compensator device made up of two lag-lead transfer function which is sed to compensate the phase lag between the excitation voltage and the electrical torque of the synchronous machine.
Multi Brand Power System Stabilizer
The disturbances (fault, noise etc ) occur on a power system produces various electromechanical oscillation modes on synchronous generators. These
electromechanical oscillations lie in the range of 0.05 to 5.0 Hz frequency range. MB-PSS are used to tune different mode of frequency oscillation and improve the stability of
Delta W PSS
Delta Pa PSS
The MB-PSS made up of the transducer, the lead-lag compensator, the transducer and the limiter.
Speed deviations of two transducers are used to feed three band structures
Fig 2. Synchronous generator model with PSS
III POWER SYSTEM STABILIZER
In the literature of PSS, there are many methods for frequency control of power system using PSS. In this
Fig 6. Membership function for Acceleration power (Pa)
Fig 4. MB-PSS
Low band for slow oscillating phenomena (0.05 Hz)
Intermediate band for inter area mode (0.2-1.0 Hz)
High band for local modes like plant or machine (0.8-4.0 Hz).
Simplified diagram of the MB-PSS is given in figure 4. [1,2].
Fuzzy Logic Controller (FLC)
Now a day, fuzzy logic is emerging as a powerful tool. It is basically used to maintain the power system stability. It is in the form of many valued-valued logic which is based on degree of truth. Truth sets allows the objects to get grades of membership from zero to one (true or false). These sets are mainly represented in terms of linguistic variables which is ordinary language being used to represent a specific fuzzy set in a problem such as large, medium and small[9-14].
Fuzzy logic is a flexible approach and its concept is easy to understand.
The fuzzy logic power system stabilizer is comparatively more robust than the other power system stabilizer. It has lower settling time then the other methods. The proposed FL-PSS has two input namely acceleration power and rotor speed deviation of synchronous machine. Its give voltage as the output. Membership functions for input and output are shown in the figure 5,6,7. Rule table is also given in table 1.
Fig 5. Membership function of rotor speed deviation (dw)
Fig 7. Membership function of output Voltage (Vstab)
TABLE-1: Rule based table for the Fuzzy Logic Controller
IV SIMULATION RESULT
machine New-England Power System as shown in figure 1 is being considered for this work.
The model of the synchronous generator with different type of PSS (conventional PSS, MB-PSS, FL-PSS) is being tested under different conditions.
The system was subjected to a disturbance 3 phase fault condition (with and without noise). We have studied the variation of above. Rotor speed deviation and Rotor speed of generator 1 is as shown below. It also show the rotor speed of generator 10-8 (local-area mode) generator 10-3 (inter-area mode) as shown in figure 12 and 13.
Fig 8 Rotor Speed Deviation (d\omega) of Generator 1(Without noise)
Fig 9 Rotor Speed Deviation (d\omega) of Generator 1(With noise)
Fig 10 Speed of Rotor in Generator 1
Fig 11 Speed of Rotor in Generator 1(with noise)
Fig 12. Rotor Speed (a) 810 (without noise) and (b) 810 (with noise) on local mode
TABLE-II: Comparison of rotor speed of different technique (local-area mode)
Greater than 20
Delta w PSS
Greater than 20
Fig 13. Rotor Speed (a) 103 (without noise) and (b) 103 (with noise) on inter-area mode
TABLE-III: Comparison of rotor speed of different technique
Greater than 20
Delta w PSS
In this paper, a design scheme of power system stabilizers for synchronous machine (10 generators) with 39 buses using different type of PSS model is given. It also shows the inter-area and local area mode of interaction. Comparison of control techniques (CLPSS and MB-PSS) has demonstrated that the proposed technique (FL-PSS) have lower setting time, more robustness against parameter variations and external disturbances, increase the power transfer limit of the system than the conventional. Improving the efficiency, controlling the frequency, system stability and reliability of system. For the further increment of stability we can use Neuro or Fuzzy-neuro control technique.
I.Kamwa, R. Grondin, and G. Trudel, "IEEE PSS2B versus PSS4B: the limits of performance of modern power system stabilizers," Power Systems, IEEE Transactions on, vol. 20, pp. 903-915, 2005
R. Grondin, I. Kamwa, G. Trudel, L. Gerin-Lajoie, and J. Taborda, "Modeling and closed-loop validation of a new PSS concept, the multi-band PSS," Power Engineering Society General Meeting, 2003, IEEE, vol. 3, p. 1809, 13-17 July 2003 2003.
Pooran Singh Shekhawat, M. P. Sharma, Bharat Bhushan Jain,
Increase of Transient Stability of Thermal Power Plant with
Power System Stabilizer, International Journal of Scientific & Engineering Research, Volume 5, Issue 10, October-2014.
A. Moeini1, I. Kamwa, P. Brunelle, G. Sybille, Open Data IEEE Test Systems Implemented in Simpower Systems for Education and Research in Power Grid Dynamics and Control, Power Engineering Conference(UPEC), 2015 50th international universities,1-4 Sept.2015, Staffordshire university, UK.
http://sys.elec.kitamiit.ac.jp/ueda/demo/WebPF/39-New- England.pdf (accessed April, 2015)
http://www.mathworks.com/products/simpower/index.html (accessed April, 2015).
Avishek Paul, Mahendra Bhadu, Nilanjan Senroy, Abhijit R.Abhyankar, Study of Effect of Local PSS and WADC Placement Based on Dominant Inter-area Paths, 2015 IEEE
Dmitry Rimorov, Innocent Kamwa, GÃ©za JoÃ³s, Model-based tuning approach for multi-band power system stabilisers PSS4B using an improved modal performance index, IET Gener. Transm. Distrib, 2015, Vol. 9, Iss. 15, pp. 21352143 & The Institution of Engineering and Technology 2015.
Siraparapu.Satyanarayana, R.K.Sharma, Mukta, Sappa.Anil Kumar, Automatic Generation Control in Power Plant using PID, PSS and Fuzzy-PID controller, IEEE 2014
Mahendra Bhadu, Bhuvnesh Rathor, S. K. Bishnoi, Modern Control Techniques of AC Microgrid, 2017 IEEE .
Manish Kushwaha, Ranjeeta Khare, Dynamic Stability Enhancement of Power System using Fuzzy Logic Based Power System Stabilizer, 2013 International Conference on Power, Energy and Control (ICPEC).
M. Mary Linda, N. Kesavan Nair Dynamic stability enhancement with fuzzy based power system stabilizer tuned by hottest non-traditional optimization technique, Computing Communication and Networking Technologies (ICCCNT), 2010 International Conference , Karur, India.
D. K. Sambariya, Rajeev Gupta, Fuzzy Logic Based Power System Stabilizer for Multi-machine System, Conference: Thirteenth, National Power Systems Conference (NPSC-2004), At Chenai, India.
Arun Kumar Sahu, Vishwanath Prasad Kurmi, Stability Enhancement of Power System using Fuzzy Logic Based Power System Stabilizer International Journal of Science,Engineering and Technology, 2017, Volume 5 Issue 3.
Y. Chompoobutrgool and L. Vanfretti, "A fundamental study on damping control design using PMU signals from dominant inter area oscillation paths," North American Power Symposium(NAPS), 2012,pp.1-6, 9-11 Sept. 2012.
Agung Bundi Muljono, I Made Ginarsa, I Made Ari Nrartha, Stability Enhancement of a Large-Scale Power System Using Power System Stabilizer Based on Adaptive Neuro Fuzzy Inference System, World Academy of Science, Engineering and Technology, Internation Journel of Electronics and Communication Engineering Vol:10, No:10-2016.