 Open Access
 Authors : Manas Redij , Sanjay N Havaldar
 Paper ID : IJERTV11IS010108
 Volume & Issue : Volume 11, Issue 01 (January 2022)
 Published (First Online): 01022022
 ISSN (Online) : 22780181
 Publisher Name : IJERT
 License: This work is licensed under a Creative Commons Attribution 4.0 International License
Investigation of Heat Transfer Enhancement in Tube Heat Exchanger by using Outer Helical Fins and Helical Inserts
Manas Redij, Sanjay N Havaldar
School of Mechanical Engineering
Dr. Vishwanath Karad MIT World Peace University, Pune Pune, Maharashtra, India411038
AbstractIn this paper, the performance of a double pipe heat exchanger with helical fins and Helical inserts are investigated analytically.The study is to investigate the heat transfer coefficient and pressure drop for fins and insets configuration.The analysis is conducted for set values of diameters of pipes which gives the optimum Reynolds number for the flow to be in turbulent nature.The model was first validated for a simple double pipe heat exchanger by comparison with empirical correlations and was then used to investigate the helical fins and inserts effects having pitch (300500mm).The results obtained provide enhanced heat transfer performance and highpressure drop compared to large pitch of insert.Also empirical correlations expressing the results were developed based on curve fitting.
Keywords: Double Pipe Heat exchanger, Heat transfer enhancement, Double pipe HX ,Helical fins, Helical Inserts.

INTRODUCTION
In todays world, the heat exchanger are one of the most widely used heat transfer equipment used varying its usability from automobile industry to chemical plants to power generation and many more. A simple double pipe exchanger consists of Two pairs of concentric pipes,the two uids that are transferring heat ow in the inner and outer pipes ,respectively. Tubular heating is mainly used in applications such as plastic injection and rubber molding, packaging, plastic welding, plate heating.Heat Exchanger must have lower costs and higher energy efficiency.
Recently various studies have been done on heat transfer enhancement in heat exchangers, M C Wang et al[1] used helical baffles in shell and tube heat exchanger having parameter as folded helical baffle with electric heater with long utube.They have used the helical baffle with No perforation and none of the insert was used.The Helical baffle technique was quite effective and with helix angle being 25, it was most effective.Flow resistance was lesser than ordinary baffles and there is scope of improvement in results by using various inserts. Recently in 2017 Maakoul et al [2] investigated Helical baffles in double pipe HX having Baffle spacing of (100,50,25) on annulus side.The results were 5%, 17%, 30% and 45% on average with an increase in pressure drop equal on average to 2, 5, 11 and 20 time the pressure drop in a conventional HX.The scope of work was by increasing the length of the tubes , its effect on the pressure drop and heat transfer can be studied.In 2012 Thianpong et al [3] studied Perforated Twisted Tape insert in tube HX and tested for Perforated Twisted Tape with diff. Twist ratio, Pitch ratio and Dia ratios.The results proved
that TPF decreases with increase in the tape twist ratio and pitch ratio.But at high Re TPF was observed to be less than unity which is not good. The length of the perforated insert was kept constant, so there is a scope of varying the length of the insert and getting the results at different ratios.In 2016 Chang et al[4] studied the thermal performances of turbulent tubular flows enhanced by ribbed and grooved wire coils.In this they used R90; G90 ,G45, RG90 augment for experiment.Due to separated flow which is generated by rib flowed through groove resulting in enhancement of thermal performance.The result was that TPF of R90,R45,RG45 was more than unity and G45 had the best performance in increasing TPF.The length of the insert was kept small.So the length variation can be obtained and also use of the software can justify the results.In 2013 Nanan et al[5] studied the Co and Counter Helical Twisted Tapes in tube HX where Twist ratio was 35 and angle was 30 to 90.It was found that at constant Re counterswirl gets better than coswirl. Counterswirl consistently leads to significantly higher friction factor than the use of Coswirl, as counterswirl generates higher flow hindrance.The TPF obtained by Coswirl insert are slightly good than those given by counterswirl insert (up to 4.7%).As the result, they suggested that combined enhancement of TPF and all the factors was much more than the individual enhancement. Saha and Dutta[6] studied a circular tube having short length and smooth pitch and observed that friction factor and Nu increases with using augment. In 2018 Bhumina [7] investigated for twisted tape and found out that uniform twisted pitch performs better than varying pitch augment. Wang and suden [8] tested for circular pipe HX with twisted tape regularly spaced and found out that larger number of turns may yield improved thermohydraulic performance compared with single turn.Seigel[9] investigated that for tube HX horizontal insert in tube HX increases heat transfer rate more than vertical inserts.Bolla et al[10] found in this studies that while experimenting with ribs and tapes, the ribs performed better than tapes.Burfoot et al[11] He investigated that twisted tape for roughness in tube HX and found that surface roughness of inserts affects the thermophysical. Haruki [12]He tested wire coil in Tube HX and results were that pipe friction and heat transfer coefficients varies by values of velocity,pitch and length.Olvister and sahoji[13] investigated nonnewtonian fluid in tube HX and found a drop in TPF by margin of 12%. From literature study, it is seen that researchers have used various method to increase the heat transfer efficiency of tube heat exchager.But in order to improve the Thermal performance of the HX we can to evaluate the effect of two
augment on a single setup.so that we can compare the results with the previous work to see the actual margin we have achieved.

NUMERICAL MODEL

Physical Model
The aim of the research is to study the effect of Helical inserts of different pitch and outer helical fins in tube heat exchanger. As there is change in dimensions of HX so, the pressure and velocity along the tube heat exchanger changes and thus the amounts of heat transfer rate and pressure drop changes. The configuration of helical insert in doublepipe
heat exchanger are shown in fig 2, the insert pitch B varies from 25 to 100 mm (top to bottom order).It is seen that geometry of HX is simple but its numerical thermohydraulic study is complex due to the complexity of flow regime in the annulus and inner tube side.
The cold water flows on the tube side, while the hot water flows in the annulus side in a countercurrent configuration. The length and diameters of the modeled heat exchangers are kept the same with each other, which is to ensure all of the values of geometry parameters are consistent except the pitch of helical insert. The material of the heat exchangers parts is stainless steel considering all the factors.The fig 1 shows the geometric representation of the flow arrangement and gives the idea about the placing of outer helical fins and helical inserts.The diameter is calculated by considering the turbulent flow condition in picture, which will help in increasing the chances of heat transfer rates.The CFD software Fluent and design modeller were adopted to establish the models and analyze the flow and heat transfer properties.

Governing Equation
Water is used as it is a incompressible fluid with constant properties. Furthermore, the fluid flow and heat transfer processes are considered in the turbulent regime and steadystate case, within the calculation range, ll RE are greater than 5000 for inner pipe and greater than 3000 for annulus region. The leak in between helical wall and the annulus pipe is very small and can be neglected.
This model was based on the numerical solution of continuity, momentum and energy equations.
(a)
Fig 1. (a) Geometry of Double pipe HX with Helical fins and Helical inserts
Fig 2. Helical inserts of varying pitch (10025mm)
Table 1. Operational parameters
Sr. No
Dimensional parameter
Dimension
1
Heat exchangers capacity
25kw
2
Temperature range
2090
3
Length of Heat exchanger
1000mm
4
Working fluid
water
5
Flow type
Counter clock flow
6
Flow condition
Cold water inside
Continuity Equation:
(b)
(b) Design of Helical fins on outer tube and inserts in inner tube Momentum Equation:
Energy Equation:
where u; T and p represent the fluid velocity, temperature and
pressure, respectively. q is the fluid density, m and Pr are the fluid kinematic viscosity and Prandtl number, subscript turb refers to turbulent flow.

Domain definition, Mesh sensitivity, Boundary condition. In paper 5 doublepipe heat exchangers are studied consisting One simple doublepipe exchanger and the others have helical inserts with different pitch(25100mm) on the inner side of the pipe.For each of the 5 studied heat exchangers, three domains are defined, two fluid domains (water in the inner tube and water in the annulus side) and one solid domain (walls, baffles).The mesh used is a mix of unstructured tetrahedral and wedge (Prism) grid .So due to wedge elements results in use of inflation layers and are located near the walls.
In order to ensure the accuracy of the numerical results, the mesh sensitivity test was conducted for B= 50 mm. A series of grid sensitivity tests were carried out to ensure that optimized computational mesh was obtained.
Table 2. Mesh metrics
Nodes
Elements
Avg. Skewness
Orthogonal
24805
131209
0.209
0.867
The Boundary is set having zero slip and zero edging. The walls represent the solidfluid interaction between the two fluid domains and the solid domain two interfaces with coupled wall.
The outlets are kept to zero pressure so the inlet pressure is equal to the pressure drop on both sidesThe algorithm of simulation is kept simple to avoid any calculation glitch and further error addition as if we increase the complexity, the error also multiply and the results obtained are not upto the mark which is not acceptable in CFD analysis .
(a)
(b)

DATA REDUCTION

The Heat transfer for tube side(cold fluid) is given by
Where is the mass flow rate of cold water, is specific heat of cold water and is Temperature difference between cold water inlet and outlet.

Heat transfer for annulus side (hot fluid) is given by
Where is the mass flow rate of hot water, is specific heat of hot water and is Temperature difference between hot water inlet and outlet.

Flow Velocity is calculated as
Where m is the mass flow rate, is density of water and Area of flow section is given by .

Reynolds number (Re) is calculated as
Where is dynamic viscosity.

Hydraulic Diameter is calculated by
Where is contact area of flow and P is the wetted perimeter.

For helical fins annulus side area is given by
Where B is the pitch of the outer helical fins, is internal diameter of annulus side and is outer diameter of inner tube.
(c)
Fig 4. Mesh, (a) Body . (b) Helical fins . (c) Helical insert

Nusselt number(Nu) is given by
Where h is the heat transfer coefficient, d is the diameter and k is thermal conductivity.


RESULT AND DISCUSSION
In this study thermal and performance of heat exchanger is analyzed using CFD simulation and numerical analysis. The
study takes into account the temperature range of 2227 for cold fluid and range of 8590 for hot fluid.Flow rate was varied from 0.1 kg/s 0.3kg/s for bot hot and cold pipes.Nusselt number validation for both inner tube and annulus side was done using the following correlation:
[8]

Reynolds no.(Re) Variation with cold water inlet( ):
Fig 5. Re vs
Reynolds number is important parameter while studying the heat exchangers.From the above result it is observed that as we increase the inlet temperature of cold fluid, the reynolds number increase non linearly.This is because as we increase the inlet temperature, decreases and it results in increase
in ,as heat exchagers capacity is fixed.so due to increase in
, reynolds number increase.

Reynolds no.(Re) Variation with hot water inlet( ):
The hot water inlet is important inputs which use in heat exchangers.After analyzing the graph it is clear that as we increase the hot water inlet , the reynolds no. Decreases.This is because as we increase the from 85 to 90, the increases which results in decrease of as capacity is fixed.so this results in decrease of reynolds number.
Fig 6. Re vs
5.3 Cold pipe pipe Dia variation with cold water inlet(
):
Fig 6. di vs
The diameter selection of pipes is important factor while designing the heat exchangers. The diameters are selected such that it will enhance the chance of improvement. From the above fig. It is clear that the temperature range which we used for cold inlet(2227), the favourable diameters for inside pipes inner diameter is ranging from 78.2 to 89mm.So from this the diameter was selected to be 88.9mm considering the standard size availability in market.

Hot pipe pipe Dia variation with hot water inlet( ):
The diameter selection of pipes is important while deciding the geometry of the heat exchangers. The diameters must be selected such that it will enhance the chance of improvement. From the below fig.,It is clear that the temperature range which we used for hot inlet(8590), the favorable diameters for outside pipes inner diameter is from 125 to 131mm.So thus, 127mm is taken as per availability in market.
Fig 7. Di vs
Fig 8

Heat Transfer Performance:
Fig 8 represents the comparison of heat transfer coefficient for all four conditions of helical inserts having pitch from 25100mm.It is observed that the heat transfer coefficient increases with the increase in the mass flow rate inside pipe.The heat transfer coefficient also varies inversly with pitch of helical insert. As we decrease the pitch of helical insert from 100mm to 25mm , the heat transfer coefficient
increase.This is due to higher fluid average and maximum velocities when using helical inserts of smaller pitch.Thus use of helical geometry improves H.T in this condition.
Fig 9.Velocity streamlines for different pitch of insert.
5.6 Pressure Drops:
Fig 10. Pressure drop variation
The pressure drop is of great importance in the design of heat exchanger and also pumping cost is highly correlated to pressure drop,
and therefore lower pressure drop results in lower operating costs.Fig 10 depicts the variation of the pressure drop versus the mass flow rate for the studied cases.As expected previously, the use of helical inserts results in a higher pressure drop, which is equal to on average of 2, 5, 11
and 21 time the pressure drop for a conventional flow, for B equal to 100 mm 50 mm, 33.3 mm and 25 mm respectively.This high pressure drop is caused by: (1) The decrease in annulus fluid path, notably for lower B values (2) high average velocity in the annulus side as a result of the reduced flow area (3) the sudden change in flow area at the inlet side (5) higher maximal velocity at entrance region (4) a larger contact surface between the fluid and the solid walls due to the addition of the helical geometry. The fluid which is in the layer is in contact with the solid walls (tubes and insert walls) will come to a complete stop. This results in slowing down of particles, thus, increasing the pressure drop.

CONCLUSION
In the present study, a tube heat exchanger with helical insert and fins was studied analytically and CFD analysis was performed to evaluate the performance of the HX. It was found out that using the insert on smaller pitch increases the heat transfer efficiency by 5% than the conventional one. But also with the inserts of smaller pitch, the pressure drop is high.The turbulent regime was considered thought the study for making it closer to real situations.
Further points which must be studied are (1) The optimum combination of outer fins and inserts for enhancement.(2) Length variation can be studied keeping same condition.(3)Effect of change in helical insets and fins geometry such as thickness and inclination angle.
NOMENCLATURE:
Inside diameter of inner pipe Outside diameter of inner pipe Inside diameter of outer pipe Outside diameter of outer pipe
B Pitch of insert
h Average heat transfer coefficient Re Reynolds number
Nu Nusselt number Pressure drop
k Thermal conductivity
Subscript:
In Inlet
Out Outlet turb Turbulent
REFERENCES:

Heat transfer enhancement of folded helical baffle electric heaters with oneplustwo Utube units. Lab of Thermal Conversion and Control of Ministry of Education, School of Energy and Environment, Southeast University, Nanjing, China.

Numerical design and investigation of heat transfer enhancement and performance for an annulus with continuous helical baffles in a doublepipe heat exchanger Anas El Maakoul. College of Science and Technologyr, Morocco. REAM Laboratory, International University of Rabat Sale, Morocco.

Heat transfer and thermal performance characteristics of heat exchanger tube fitted with perforated twistedtapes Chinaruk Thianpong ,.Heat Mass Transfer (2012) pg 48:881

Thermal performances of turbulent tubular flows enhanced by ribbed and grooved wire coils , Thermal Fluids Laboratory, National Kaohsiung Marine University, No. 142, Haijhuan Road,, Taiwan, Department of Marine Engineering, National ohsung University.

Heat transfer enhancement by helically twisted tapes inducing co and counterswirl flows, Department of Mechanical Engineering, Faculty of Engineering, Mahanakorn University of Technology, Bangkok 10530, Thailand.

Wang, L. and Sunden, B. Performance comparison of some tube inserts. Int. Commun. Heat Transfer, 2002, 29, 45 56.

Seigel, L. G. The effect of turbulence inserts on heat transfer coefficients of water flowing in a horizontal tube. Heating, Piping and Air Conditioning, 1946, 18, 111 114.

Bolla, G., De Giorgioi, G. and Pedrochi, E. Heat transfer and pressure drop comparison in tubes with transverse ribs and with twisted tapes. Energia Nucl. (Milan), 1973, 20, 604613.

Burfoot, D. and Rice, P. Heat transfer and pressure drop characteristic of short lengths of swirl flow inducers interspacing along a circular duct. Chem. Engng. Res. Des., 1983, 61, 253258.

Inaba, H. and Haruki, N. Heat transfer enhancement of flow in a straight pipe with drag reduction surfactant by using wire coil. Trans. Jap. Soc. Mech. Engrs, Part B, 2002, 68, 481488.

Oliver, D. R. and Shoji, Y. Heat transfer enhancement in a circular tubes using different tube I,nserts: nonnewtonian fluids. J. Chem. Engng. Res. and Des., 1992, 70, 558 564.